Question about Heating & Cooling
SOURCE: pilot light will not light
Sounds like you may need a new electronic control module. This is a rectangular shaped plastic box that has wires coming out of it. This is what tells the pilot to light on these older furnaces.
Posted on Jan 28, 2009
SOURCE: Baxi solo 3 70pf boiler problem
This happened to me and it was a rubber pipe inside had perished so it was detecting a loss of pressure. You can see it if you take the main cover off and also the front clipped on cover. Its at the top on the right. You need to replace it with heatproof pipe. Good luck!
Posted on Jan 05, 2010
first off ensure water is getting to boiler, next, No pilot = pressure switch. On my baxi solo 40 pf pressure switch is replaced 8-10 times a year cures your problems,,,,,,,, momentarily , and have had all your other parts,but with no effect to speak of,.......sorry............ solution = [ change boiler ].sounds like gas pressure or lack of water to system or **** boiler like mine .........good luck.
Posted on Mar 11, 2010
Go to this link.Bottom of page 15 on the manual
Basically it says (turn on the power first) Turn the knob to the the star/flame marking. Push the knob in, hold it for approximately 10 seconds. Release and check the small flame is lit. Now turn it to your desired heat setting.
Posted on Jul 21, 2010
Tips for a great answer:
Nov 24, 2013 | Heating & Cooling
Jan 22, 2013 | Water Heaters
Oct 05, 2012 | Heating & Cooling
Nov 26, 2010 | Heating & Cooling
Feb 20, 2010 | Heating & Cooling
Jan 10, 2010 | M20 X-Treme Radar Detector
Dec 31, 2009 | M20 X-Treme Radar Detector
May 15, 2009 | Water Heaters
May 07, 2009 | Kitchen Ranges
539 people viewed this question
Usually answered in minutes!