Question about General Filters 1042-LH Humidifier
continous water flowing all the time. ( if humidistat is turned on)
lennox funurnace, 4 to 5 years old, 2 speed blower, mid efficiency
when I turn on the humidistat, you hear the solenoid, click, water flows non stop, regardless if the furnance is on or not.
I installed a new 24v transformer, for direct voltage to the humidifer, installed a new solenoid
the furnance company unconnected the humidifer wiring from the circuit board of the furnance, as the humidifer was taking energy needed to run the furnance the correct lenght of time. house cold at times as the furnance did not stay on long enough.
the solenoid and two brass fitting, the longer of the 2 is pointing down.
I'm lost, any suggestions appreciated.
if the wiring is correct, could there be a short in that wiring ??
Theholts220 - Sounds like they needed to install a bit larger transformer . You can also buy a A 50 Sensing relay that attaches to the wires for your motor and when you turn on the furnace it will allow the power to go to the humidistat. Very strange though they do not use a lot of power. Check and make sure the wires are not pinched or touching metal somewhere.
TLuzzo - The humidistat seems to be working when you turn it down. The wires for the solenoid should be hooked up to your furnace circuit board. The instruction manual will tell you where. If you dont have a spot on your circut board the A 50 sensing reley is they way to go. They are inexpensive
Posted on Mar 06, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 04, 2011 | Aprilaire 700 Humidifier
Feb 06, 2010 | Humidifiers
Jan 06, 2010 | Aprilaire 600 Humidifier
Dec 30, 2009 | Honeywell HE220A1019 Whole House...
Dec 07, 2009 | Aprilaire Humidifiers
Oct 12, 2009 | Honeywell HE220A1019 Whole House...
Apr 09, 2009 | Aprilaire 700 Humidifier
Mar 12, 2009 | Humidifiers
Nov 28, 2008 | General Filters 1042-LH Humidifier
718 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: