Question about American Standard Heating & Cooling
Model number TUC080B942A1
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
American Standard and Trane are the same thing. The diagram you want is not complicated at all. Just straight cool unit. American Standard does not put low or high pressure controls on unit. You can get diagram on line At American Standard.com. Just what do you need to know? Very basic unit.
Posted on Jun 12, 2009
Hi I am sure this model number is correct and it is a 3 Ton unit.Normally when the breaker trips as soon as you reset it, the compressor is compromised. Happened to me yesterday on a 5 ton heat-pump. When this happens, what you can do if you are a handy type of man, is to prove this. I don't know if the is is a split system or a all in one package unit, doesn't matter. Get to the compressor compartment. Of course the power will be off.If you can see the run capacitor, take a screw driver and short across the terminals to discharge it, as it could have a small amount of juice in it, I doubt it. Anyway, remove the plastic cover to expose the terminals. They can be hard to remove sometimes, just use a screw driver to push the clips in. Wire colors should be black for common, yellow for start, and blue for run. Write down the order they were in. To be safe, tape the metal connectors so they wont touch metal when you turn the power back on. After you have done this, turn everything back on. If the breaker holds and everything else is on, fan and so on, this proves the compressor is probably shorted to ground. If this a/c is rather new, I would replace the compressor. If it is old, I would think about getting prices on a new unit. Just food for thought. Please let me know on the out come of this test, please. When a compressor shorts out, or locks up, it draws what is called locked rotor amps/LRA which could be from 49 on up, and your breaker can be 25, 30, 35 to 40 amps so it will trip. Keep me posted and do this test, it is very easy to do.
Posted on Apr 18, 2010
Tips for a great answer:
Feb 03, 2016 | American Standard Heating & Cooling
Jul 24, 2015 | American Standard 5000 Heat Pump Unit
Jun 28, 2012 | American Standard Heating & Cooling
Mar 31, 2011 | American Standard AMERICAN STD 100 Prop...
Mar 09, 2011 | American Standard Kitchen Faucet 6310 020...
Dec 20, 2010 | American Standard Heating & Cooling
Sep 29, 2009 | American Standard 2770.018w.020 Cadet...
Jun 11, 2009 | Heating & Cooling
Jun 05, 2009 | American Standard Kitchen Faucet 6310 020...
76 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: