Question about Goodman GPH1324H21A WallWindow Air Conditioner
Worked fine last week used heat at night for a few days then it got hot out and would not cool all the blowers blow but no cool air. when i switch to hear it heats fine.but does not seam to heat on cool or cool on cool
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: goodman ac / heat pump
Goodman energizes it reversing valve in the cooling mode. Usually in the "o" circuit of the thermostat wiring.You may have that wired hot somehow.
Posted on Nov 28, 2007
When the condenser coil is dirty come high pressure and cut out the compressor, you can wash with the garden hose around the condenser coil before disconect the unit for prevent any electrocution or the sistem is overcharged
Posted on Aug 07, 2008
Look for an outdoor thermostat/temp sensor and if you find one chack to see if its adjustable. (adjustments probably found on the board.)
It could also be wired to bypass the heatpump altogether when temps are below 40.
you will want to adjust, rewire or remove that t-stat/sensor.
In some areas they are really not needed. What state are you in?
Posted on Mar 06, 2009
The reversing valve may be stuck or it has a burnt solenoid coil. Also, check the defrost relay accross the contacts with an ohmmeter and see if it's bad. Goodman heat pumps also trip on high pressure. There's a resettable switch on some units with a red button. However, I think the problem is in the defrost circuit or reversing valve. If your electric heat is on, change the board.
Posted on Apr 27, 2009
Tips for a great answer:
Oct 27, 2014 | Water Heaters
Oct 20, 2014 | Water Heaters
May 03, 2017 | Lakewood 5101 Oil Filled Radiator Heater
Jun 21, 2009 | Goodman CLQ36AR49 Air Conditioner
Jun 20, 2009 | Goodman Heating & Cooling
Jun 16, 2009 | Goodman CLJ36AR42 Air Conditioner
Nov 26, 2008 | HP Blower Fan
Jul 19, 2008 | Goodman CLQ36AR49 Air Conditioner
Mar 20, 2012 | Goodman GPH1324H21A WallWindow Air...
25 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: