Question about Electrical Supplies
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Generac Guardian 15kW Generator
That sounds just about right, if the relay contacts get welded together it sometimes takes out the driver on the printed circuit board. As you found out, 12vdc from 23 to 194 makes the transfer switch move to the Generator position, relay not energized makes the ATS move to the Normal position.
You can make a nice test function by installing a 10 amp contact switch in series with either the N1 or N2 terminals. When the switch is open the generator thinks the Normal power has failed.
Posted on Jan 26, 2009
Tips for a great answer:
Jan 28, 2015 | Generac 12kw Lp/ng Generator With Auto...
Oct 08, 2010 | Generac 100 Amp 120/240-Volt Transfer...
Jul 02, 2010 | Generac Guardian 200 Amp Transfer Switch...
Jun 03, 2010 | Generac 100 Amp 120/240-Volt Transfer...
Jan 22, 2010 | Generac 100 Amp 120/240-Volt Transfer...
Oct 03, 2009 | Generac Electrical Supplies
Sep 08, 2009 | Generac 100 Amp 120/240-Volt Transfer...
Jul 14, 2009 | Generac 100 Amp 120/240-Volt Transfer...
Jul 09, 2009 | Generac Guardian RTSE200A3 200 Amp...
Sep 22, 2017 | Electrical Supplies
199 people viewed this question
Usually answered in minutes!