Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
POssible feed back thru tstat. This sometimes happens. Take a look at tstat disconnect w or white wire that goes to heater. Turn from heat to cool and abck and see if it does it again if not change tstat. You can get a good one at Home depot or Lowes about 20.00 easy to install Keep in touch Rus
Posted on Nov 25, 2009
SOURCE: Have a rheem criterion II. Model
The way it lights is that the gas is spread from one burner to the next by either a flame tray or small holes drilled in the burner tubes. If the flame does not get all the way across the burner tubes within a few seconds, the unit goes out on failure. Clean and inspect each burner tube, not just the orifice. Clean any tray that connects the burners. You can use a small wire brush or tooth brush but be careful near the glow igniter as it is very fragile.
Posted on Dec 12, 2009
Turn off the power to furnace.
on the last burner to light there is a small metal rod in front of the burner. This is a safety called the flame sensor. It is dirty. Unscrew it from the bar ( 1 Screw) unplug the connector wire from it and clean it with steel wool. it will be kind of burnt. Plut back in place and turn on the furnace to cycle.
Posted on Apr 04, 2010
Tips for a great answer:
Dec 16, 2015 | Heating & Cooling
Feb 09, 2013 | Solar Rheem Gas Fired Pool & Spa Heater...
Jan 08, 2013 | Heating & Cooling
Feb 07, 2012 | Heating & Cooling
Mar 11, 2011 | Heating & Cooling
Feb 15, 2011 | Heating & Cooling
Feb 01, 2011 | Heating & Cooling
Apr 04, 2010 | Heating & Cooling
Dec 14, 2017 | Honeywell Heating & Cooling
133 people viewed this question
Usually answered in minutes!