Question about Goodman Heating & Cooling
The pilot light does not go out
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
depending on how old the unit is , you turn the gas valve to pilot setting, hold down the button, light and hold for 1 min.
Posted on Oct 28, 2008
SOURCE: Blower works but no heat
If in fact you have the above listed furnace, you do not have a pilot but electronic ignition. You will need to remove the front cover on the furnace, tape down the door safety switch and then have someone help you by turning up your thermostat to a very high setting. Watch and listen inside the furnace. There should be some blinking going on at the control board followed by a small blower fan starting up. Then after 10-15 seconds there should be a click followed by an orange glow viewed thru the viewing window to the burner section. In a few seconds the gas valve should click and the burners will ignite. There is a safety switch that will sense flame and then keep the gas going to the burners. If it does not sense it, it will shut it off within 10 seconds. If all is well so far, your blower will turn on in about 90 seconds after flame. There is a diagnostic code chart on the back side of the access door if you get an error code (blinking) on the control board.
Always check little things like air filter, condensate drain and broken or loose wires.
Posted on Nov 11, 2008
Does the main blower fan kick on? Also, if the heater is vented outside via a flue pipe, there may be a small (about 3 or 4 inches in diameter) vent fan that kicks on to ensure the exhaust fumes are evacuated through the flue pipe. If there's a problem with that fan, the burner won't light either.
Posted on Nov 20, 2008
Check regulator on the unit.
Check pilot unit on the heater
use soapy water to check for leaks if see bubbles turn off main gas supply valve.
always turn off gas supply before any checks or repairs are made
when all else failes call your local gas provider to check heater and gas supply
Posted on Dec 16, 2008
It has electronic ignition. no pilot light.. it uses a hot surface ignitor to light the burners. this device gets red hot (just like looking down into your electric toaster). this hot cherry red device lights your burners
Posted on Mar 28, 2009
Tips for a great answer:
Dec 24, 2014 | Goodman Heating & Cooling
Dec 05, 2013 | Goodman GMS90703BXA Heater
Sep 17, 2011 | Premiere Ranges GCK100 Gas Kitchen Range
Nov 04, 2010 | Goodman Heating & Cooling
Jan 26, 2010 | Goodman GMS80453ANA Open Flame Mid-Size...
Dec 01, 2009 | Goodman GMS90703BXA Heater
Nov 07, 2009 | Goodman GMS90703BXA Heater
Oct 24, 2009 | Goodman Heating & Cooling
Feb 21, 2009 | Goodman GMS90703BXA Heater
Nov 27, 2008 | Heating & Cooling
38 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: