Question about Goodman CKL36AR36 Air Conditioner
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
On your t-stat you have Y, W1, W2, R, O, G, B or C or X. Y is your cooling circuit and will be the same in the air handler and heat pump unit, use the yellow wire for this circuit. W1 and W2 are your back up elec. or gas heat. Depending on how many kws or heat strips you have and t-stat wires you will put the white wire to W1 in both the t-stat and air handler. W2 is for your second stage back up heat if air handler calls for it, this will be a tan or brown or black t-stat wire and goes to W2 on t-stat and air handler. R is half of your 24v control power from the transformer and is the red wire and goes to the t-stat, air handler, and heat pump. O is for the reversing valve in the heat pump that switches it from heating and cooling. You guessed it the orange wire connect to t-stat and heat pump. G is for the blower and is the green wire to the t-stat and air handler. B or C or X is known as the common which is the other half of control circuit from 24v transform it is the blue wire and goes to the t-stat, air handler, and heat pump.
Posted on Oct 09, 2008
SOURCE: GOODMAN # ARUFO49 AIR HANDLER
MOST ALL GOODMAN ( UP TO 3 TONS)INTERNAL FILTERS ARE 22" x 22" X 1". YOU CAN GET THEM ON LINE AT www.filtera.com. ALWAYS TAKE A TAPE RULE AND OPEN THE BOTTOM FILTER DOOR AND MEASURE THE FILTER RACK. MAKE SURE YOU DO NOT HAVE A RETURN-AIR FILTER-GRILLE. LARGE WHOLE -HOUSE RETURN AIR VENT NEAR OR AT YOUR FURNACE, A/C AIR HANDLELER. Joe_Rex New Member of FixYA Retired HVAC&R contractor 45+ years exp.
Posted on Apr 28, 2007
SOURCE: CONNECT AC TO AIR HANDLER
Wire tstat normaly> Take the Y off the tstat and it goes to the outside unit. The other wire from the outside init goes to the common off the transformer. This is marked with blue,brown or black. Russ
Posted on Jul 23, 2009
either bad motor ....or.... if you are lucky a bad run capacitor. you will need some sort of capacitor checker and multimeter to diagnose it further.
Posted on Oct 31, 2009
Tips for a great answer:
Nov 13, 2014 | Goodman Manufacturing Goodman ARUF48D14...
Oct 06, 2010 | Goodman CLQ36AR49 Air Conditioner
Jul 25, 2010 | Goodman Furnace Draft Inducer Blower ...
Mar 18, 2010 | Goodman CKL36AR36 Air Conditioner
Dec 14, 2009 | Refrigerators
Apr 25, 2009 | Goodman CKL24AR24 Air Conditioner
Jan 05, 2008 | Heating & Cooling
622 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: