Question about Water Heaters
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
I called Noritz error code 16 is a overheat problem. Noritz say's to flush your coil with vinegar or CLR.
Use a small pump to recirculate the CLR or vinegar through the system for 45 minutes and flush with fresh water. This worked for me.
Posted on May 12, 2009
SOURCE: Water Heater Won't Fire up
There are a few things you'll want to check:
1) make sure you have 120VAC at the outlet
2) measure voltage across the blue/white and black/white wires connected to the gfi (black box inside the unit on the bottom left or right hand side). You should read roughly 100 VAC on both sides. If you don't read voltage on the black/white wire pair, then you gfi is tripped. Look for moisture that might be shorting the gfi.
3) If the GFI checks out ok, you probably have debris clogging your flow sensor
Posted on Aug 15, 2009
This worked for me in the same situation. There is a filter inserted into main gas/ water control valve that senses water flow restriction. The sensor is connected to the gas valve. If it senses inadequate water flow it tells the gas valve to shut down so the water in the heater won't boil. Very expensive part. If you do find the filter clogged, a sediment water filter shoud be install on the inlet side of the water piping.
Posted on Oct 13, 2009
SOURCE: Noritz Tankless error code 16
The trick with these hot water heaters is to keep the filter screen clean and flush the system with CLR periodically. Code 11 is ignition error. Is your gas valve turned on?
Posted on Dec 09, 2009
This means the thermal fuse has broken and needs replacement. The thermal fuse is a white cord which wraps around the heat exchanger. It typically breaks if the unit is excessively dirty and sooted. Before the fuse is replaced you should make sure the unit is cleaned with compressed air and descaled.
Posted on Jul 15, 2010
Tips for a great answer:
Jan 17, 2018 | Noritz 7.1 Gpm Natural Ng Gas Tankless Hot...
Oct 12, 2012 | Noritz NR98-DVC-NG 100W Freeze Tankless...
Aug 02, 2010 | Noritz 6.3 Gallon Residential Tankless...
Jul 31, 2010 | Noritz 6.3 Gallon Residential Tankless...
Apr 14, 2010 | Noritz 7.1 Gpm Natural Ng Gas Tankless Hot...
Jan 24, 2010 | Noritz NORTIZ Outdoor Propane Tankless...
Jan 08, 2010 | Noritz Liquid Propane Tankless Water...
Feb 17, 2009 | Noritz 7.1 Gpm Natural Ng Gas Tankless Hot...
Jan 04, 2009 | Noritz 6.9 Gallon Residential Direct Vent...
35 people viewed this question
Usually answered in minutes!