Question about Ruud UAMB Air Conditioner
Sounds like the thermostat is hooked up wrong. If the ac doesnt work right its in the thermostat programming or the wiring. Hope this helps good luck
Posted on Aug 18, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
if the purge fan wont start on its own see if there is a capactor attached. if not replace it. more than likely you cannot lube the bearings in your blower motor. the new fans are not serviceable.
Posted on Oct 30, 2008
SOURCE: Daily reset of outside unit
I have the same unit and was having the same problem. My brother works on A/C's and told me that the coils most likely needed cleaning from the inside out because when they are clogged with a lot of debris the system will overheat and cause that switch to trip and so far it has worked. What you need to do is turn the main breaker off to the outside unit first then take the four screws out of the top of the unit, use a flat head screwdriver and lift the fan it's self up out of the carefully taking caution of the wires going to the fan, then take the garden hose with a spray nozzle and wash the coils from the inside spraying through the coil to the outside and then wash the louvers off of all the debris and this should help.
Posted on Aug 03, 2008
It sounds like you have a unit called a heat pump. When a heat pump unit is in cooling mode the outside unit blows hot air and the inside unit blows cold air. If the outside unit is blowing cold then the indoor unit is most likely blowing room temperature or warm air. It sounds like the thermostat could be controlling incorrectly or you could have a failed reversing valve which is the device that switches the unit from heating to cooling mode.
Posted on Jun 02, 2009
first look for red button neer the copper line set if has one push it second inspect thermostat wires for weed eater damage check disconnect for fuses check breaker at main panel pull disconect and remove cover check stat wire connections look at the capacitor if swelled up on top bad if all look ok put disconect in using insulated object manually push in contactor if unit comes on check for 24 volt ac on yellow stat wire to common if none stat wire could be loose at indoor unit or stat bad hope this helps you
Posted on Jun 06, 2009
If you have ice on the Line you are iced up. If coil is iced no air can get thru. Now First. Turn of ac and turn fan to on posotion. That will thaw unit. Let it run 45 minutes. That should do it. If the fan is not running you amy have a bad fan relay. One of the reason iced up unit is dirty evap, coil inside. Try to thaw it out first. You can clean the coil with a stool brush. Does not damage the coils. Good luck
Posted on Jun 09, 2009
Tips for a great answer:
Dec 12, 2013 | Ruud UBHC Air Conditioner
Jul 31, 2013 | Ruud UBHC Air Conditioner
Nov 04, 2010 | Ruud UBHC Air Conditioner
Jan 28, 2010 | Ruud UBHC Air Conditioner
Nov 28, 2009 | Ruud Central System Air Conditioner
Sep 04, 2009 | Ruud Central System Air Conditioner
Jul 26, 2009 | Heating & Cooling
Oct 29, 2008 | Ruud Heating & Cooling
Aug 08, 2013 | Ruud UAMB Air Conditioner
270 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: