Question about Pool & Spa
115 volt and 230 volt wiring diagrams
Posted by Anonymous on
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Thank you for posting your question here on Fixya.com.
I sent the number to my AOSmith tech contact. I hope to have it monday sometime. Please contact me thru our site, www.arrowmotor.net, so I have your email address to forward the connection diagram to.
If this answer does not fix your problem, please comment with additional details prior to rating the answer. Positive feedback is appreciated once your problem is solved!
Posted on Jun 13, 2010
I assume you mean the white wire under the rear motor cover? If so Sta-Rite puts a wiring diagram inside this back cover. Hopefully it is still intact for you. Depending on your model and if it is wired for 115vac or 220vac will make a difference. I would suggest you go to the link I attached and look up your manual. The manual will have the wiring diagram for you.
I hope this helps you out. Please rate my response. thanks
Posted on Jun 17, 2010
SOURCE: My pool originally had a
Is it going to run on 230V then? If so you would normally use red and black. The white wire should be a neutral and the ground wire is obviously ground.
Do you have a meter you can use to confirm the voltage between the wires? If you do you'll want to start with red and white since you seem to think black was not being used before. If the voltage reads 230 and the motor is set up for 230 then attach one wire to L1 and the other to L2...it will not matter which is connected where as long as one is on each terminal. Insulate the black and ground the ground lead to the motor ground screw.
If the voltage is not 230 between those two check between red and black. If that is the 230 then insulate white and put red and black to L1 and L2.
Posted on May 24, 2011
Tips for a great answer:
Nov 04, 2017 | HP Air Tools & Compressors
Aug 15, 2014 | Air Tools & Compressors
Feb 11, 2014 | Air Tools & Compressors
Dec 04, 2017 | Pool & Spa
May 25, 2012 | Plumbing
May 10, 2012 | Air Tools & Compressors
Feb 18, 2011 | Ingersoll Rand - Rand Type - 30...
Oct 07, 2010 | AO Smith 1 1/2 HP 115/230V 56C Replacement...
Jun 11, 2010 | Air Tools & Compressors
178 people viewed this question
Usually answered in minutes!