Question about GE Zoneline AZ55H09D Air Conditioner
My luxpro psd111 thermostat shows aux heat and is not warming the house. I've replaced the batteries and filter, to no avail.
What does it mean when it shows AUX HEAT?
A heatpump has two sources of heat. One is when the heatpump is operating in normal heat mode, and the other is typically electric heat strips.
The strips come on when the unit is going into defrost, when the unit is not able to keep up with the demand for heat (really cold temps) and when the unit is not working properly.
Whne the strips are on, the T-stat displays "aux-heat" to indicate the strips are in operation.
If the strips are working properly you should have warmer air than with the HP alone. Try switchin it from "heat" to "emergency heat" and see what it will do.
When the HP is not able to keep up with the demand for heat then the heat strips come on, but they typically come on only when the room temp has gotten well below the thermostat setting.
In that situation it would be normal to see indoor temps at 63 degrees when the T-stat is set on 70.
But when you set it to E-heat it bypasses the heatpump operation and goes directly to the heat strips. If they are working properly it should maintain an accurate temp in the home.
Posted on Jan 23, 2009
It means you have a heat pump and the primary system is not working properly or it cant keep up so it turns on aux heat if it is could i suggest putting it on emergency heat and that should heat your house until you can have a sevice man check it out as heatpumps can be complicated
Posted on Jan 23, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 20, 2014 | Cars & Trucks
Nov 15, 2013 | Cars & Trucks
Oct 24, 2013 | Heating & Cooling
Apr 21, 2010 | Honeywell Heat/Cool Thermostat
Mar 04, 2010 | Heating & Cooling
Jan 04, 2010 | Honeywell Electronic Programmable...
Oct 16, 2009 | Ruud Central System Air Conditioner
Apr 07, 2009 | Kenmore Heating & Cooling
Nov 19, 2008 | Honeywell Electronic Programmable...
9,495 people viewed this question
Usually answered in minutes!