Question about Ruud Gas Furnace - Excellent Condition - $350 Obo
Sounds like a dirty flame sensor, on thenopposite side of the igniter there will be a metal rod, clean this rod with steel wool
Posted on Jan 17, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
does the furnace ignite?? your system may not have been lighting and has gone into ignition lockout count the codes of the led lights then remove panel led diagnostic codes are listed there.
if led codes indicate no problem verify capacitor is good and that mtr is getting 115 volts.
Posted on Nov 22, 2008
Again is this a spark or a glow coil? If it is a glow coil look at the coil and see if there is a crack or white spot on it. If so it needs to be replaced.
Posted on Jan 18, 2009
SOURCE: Ruud furnace won't stay lit.
Hi, welcome to Fixya. If you have spark ignition turn off the power and using sand cloth clean the rod(s) and hood of the spark ignition. If it is a Hot Surface Igniter (glow coil) look on the opposite end of the burners and you will see a rod protruding in to the flame. It's called a flame sensor. Clean it with the sanding cloth. If either of these works then you bought some time but should consider replacing the part fairly soon. Please report back to let us know your progress. Good luck.
Posted on Jan 25, 2009
On a call for heat, the 24 volt thermostat sends a signal to the control module. The control module will indicate a call for heat with a light on the control either blinking or remain solid depending upon model. The inducer (exhaust) blower will purge all gasses from the furnace and pressurize a pressure switch. Once the pressure switch tells the module to continue, the electronic ignition will energize and send 120 volts to the igniter. The igniter will glow and you will be able to see it if viewed thru the small inspection port. Once the igniter gets hot enough, it sends a signal to the module opening up the gas valve (24 volts). Either a pilot will come on or the burner tube will ignite then spread the flame to all burners. Lastly a safety sensor will be looking for a certain temperature within a few seconds and the furnace will continue to operate and the room air blower will turn on in a minute or two.
What could go wrong? The unit will not run if there is no signal from the thermostat (bad thermostat or broken wire), the control module does not sense a signal from the thermostat (bad control), the inducer does not energize (bad motor), the pressure switch does not close (blocked vent piping, bad switch, plugged condensate hose), the igniter does not energize (bad control, bad igniter), the gas valve does not open or there is no gas (bad gas valve, broken wire, no gas), the pilot does not light (dirty pilot), the burner does not light (bad burner, plugged orifice, not enough combustion air), the flame does not spread to each burner (bad flame spreader, dirty flame spreader, more bad burners), the flame safety sensor does not detect flame (dirty or bad flame spreader, bad flame sensor, broken wire, bad control), or the room air blower does not energize (bad fan motor, bad control).
Posted on Jan 08, 2010
Testimonial: "Your initial response was very insightful but I didn't give it 4 since I need to know how to check the safety switch out. Thanks for your followup."
Problem: Your furnace will not
ignite the gas to produce heat for your home. When a furnace has a bad ignitor
what I see most of the time is the following sequence of operation:
1. Thermostat calls for heat. 2. Draft inducer motor starts. 3. Pressure switch attached by a small plastic or rubber tube senses the negative pressure produced by the draft inducer and closes. 4. Draft inducer runs for 30 seconds to a minute before you hear a gas hissing sound. The ignitor did not glow, the flame sensor (a small metal probe about 1/8" in diameter, with a white porcelain base) does not sense the flame, so after 8 to 10 seconds the hissing sounds stops with no ignition of gas to heat your home. Your furnace shuts down and goes into a lock out condition until you turn your power switch back off and on again. Then the sequence starts all over again with no ignition of the gas. Solution: You probably need to purchase and install a new ignitor. I would suggest that you inspect your ignitor closely for cracks. Make sure you do not touch the ignitor with your bare hands. If you do not visually see a crack, then you could have a furnace control board problem or a limit, rollout switch problem. The furnace's control board might not be supplying the voltage to the ignitor. If your furnace lights and the gas stays on for 8 to 10 seconds, then shuts right back off, then you need to clean your flame sensor with light sand paper or steel wool. You might need a new flame sensor, but most of the time they can be cleaned an will work well after cleaning.
Posted on Nov 26, 2010
Tips for a great answer:
Oct 26, 2013 | Gibson KG7TC060D24B 60,000 BTU 95.1% Gas...
Oct 19, 2013 | Heating & Cooling
Dec 05, 2010 | Heating & Cooling
Mar 03, 2010 | Ruud Matching Split Air Conditioner
Feb 16, 2010 | Dayton Gas Furnace Heater
Jan 09, 2010 | Ruud Heating & Cooling
Jan 08, 2010 | Ruud Heating & Cooling
Nov 23, 2009 | Heating & Cooling
Oct 20, 2009 | Ruud UBHC Air Conditioner
Dec 07, 2008 | Honeywell Power Humidifier: Furnace...
345 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: