Question about Tools & Hardware - Others
Posted by Anonymous on
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
I would suspect the air pressure differential switch. It looks like a diaphragm with a piece of tubing running to it and a electric switch mounted on it. Before changing it though, check that the condensate drain trap has water in it. I know that sounds silly, but if there is no water in the trap (if it's desperate from AC trap, then it can dry out in summer) you can be pulling air through the trap, and not enough pressure differential to trip switch. Also be sure the intake is clean outside. If there is any kind of Screen on intake be sure it's open. You can test switch with tester to see if it is the problem. The switch should close after the draft inducer fan starts.
Posted on Oct 08, 2010
Tips for a great answer:
Jan 23, 2011 | York Furnace Draft Inducer Blower Fasco #...
Oct 08, 2010 | York Furnace Draft Inducer Blower Fasco #...
Nov 28, 2009 | York Furnace Draft Inducer Blower Fasco #...
Nov 18, 2009 | York Yankees Bedding MLB Comforter
Jun 20, 2009 | York Furnace Draft Inducer Blower Fasco #...
Jun 10, 2009 | Heating & Cooling
Jan 16, 2009 | York Yankees Bedding MLB Comforter
Dec 27, 2008 | York Yankees Bedding MLB Comforter
405 people viewed this question
Usually answered in minutes!