Question about Amana DigiSmart PTH153B35AM Thru-Wall/Window Air Conditioner
No display when +/- switched held down and Off, Cold or heat button is depressed.
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: My Amana Prestige Ultra Central
Ok sounds like your transformer is not working. Now as long as no one has removed the doors to the furnace cabinet and they are in place just like the are suppose to be, because there is a door switch that turns off the power to the whole unit until the door is in place correctly. Find the circuit board and look to see it you have a fuse on the board it will look like a car fuse the spade type they are 5 amp fuses. If it is good find the transformer and replace it. If you feel comfortable around electricity there are two sides to the transformer line voltage which is 120 and the secondary side which is 24 volts. If you have a volt ohm meter ohm out the transformer each side line side and low voltage side. An open on either side will be noticed and then replace the transformer. I know this is alot of things to check but just elimanating everything it could be before condemming the transformer. Turn the main breaker off and replace.
Posted on Nov 27, 2008
Sounds as though the power cord reset switch might be bad and need to be replaced. If not, then there is a short somewhere in the system. Do an ohms test on the switch to determine if it is bad.
Posted on Mar 17, 2009
First off, you need to unplug power from the unit before handling anything on it, not just the master switch on the control board. There is still live power being fed to the unit while it is plugged in!
Now, the clicking sound you are hearing is a faulty relay on the control board. You have to replace the control board. The new ones are available from Amana/Goodman Mfg.. You will find, assuming you have more of these, your other units are going to start doing the same thing. It will be the same problem. When they send out the new control board, make sure you program the board. They no longer come pre programmed. It is actually a huge improvement on the older control board upgrades. Hope this helps, I have 140 of these in my hotel, I know them all too well. Let me know if you have any other questions and please rate this as a fix ya.
Posted on Apr 07, 2009
SOURCE: Amana Heat Pump Tripping Breaker
My guess I would say, you either have a wire that is short to ground or if the contacter pulls in, then I would say the compresser is short to ground.There also could be some capacitors that could be short.
Posted on Apr 07, 2009
Tips for a great answer:
Jun 16, 2013 | Frigidaire Affinity 5.8 Cu. Ft. Electric...
Oct 08, 2012 | Dometic Rooftop RV Air Conditioner
Jan 02, 2012 | 2004 Lexus ES 330
Feb 02, 2018 | LG FLATRON W2252TQ-PF 22" LCD Monitor
Oct 14, 2017 | Eaton ARC FAULT CIRC BREAKER
Jun 02, 2011 | Amana AP095R Portable Air Conditioner
May 22, 2011 | Frigidaire FAS257S2A WallWindow Air...
May 05, 2011 | Fedders A7DH45B2A Dehumidifier
Jan 11, 2011 | Amana PTH123B25AJ Heat Pump Air...
May 06, 2010 | Exercise & Fitness
71 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: