Question about Weather King 10AJA3601AH Air Conditioner
I have 4 codes flashing what is it
If you shut off the power and turn it back on does it start and run? if so, replace you air filter. Odds are the blower is dirty and if it is dirty the secondary heatexchanger is dirty and if you have a/c your a-coil will most likely be a bit dirty too. And it all starts with the ducts, there is only one place the dirt comes from. This causes bad air flow over time and could be causing your problem. But in order to do this have a hvac company come in and clean it. Find someone who does furnace and duct cleanings. I own a heating, cooling and duct cleaning business and see this all the time. a way to check the air flow is to take the return tempature and the plenum tempature. if the unit is running on high it prob should be around 70-75F diff. The sticker inside the furnace will tell you the proper temp rise.
Now if the rool out switch on the side of the burner box is tripped call a tech and have them check the heat exchanger. a burner tube is most likley gone, but this is very unlikely.
Let me know what you find...
Posted on Jan 22, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: York, diamond 90 heating issues!
Look at the electrical schematic on the inside cover to the electrical compartment. It should have a list of fault codes. Locate the condesate drain lines (up to three) and remove them and inspect them for debris/blockage. Clean them and flush them with warm water and clorox solution. Make sure that your condensate line is not blocked and that you are getting drainage from the condensate line. The new high efficiency furnaces generate a great deal of condensate water from the burner and it needs to drain properly.
Posted on Jan 29, 2011
Tips for a great answer:
Dec 06, 2013 | Heating & Cooling
Oct 24, 2013 | Tools & Hardware - Others
Mar 05, 2011 | Heating & Cooling
Jan 28, 2011 | Heating & Cooling
May 23, 2010 | Heating & Cooling
Mar 05, 2010 | York Furnace Draft Inducer Blower Fasco #...
Nov 04, 2009 | Goodman GMS90703BXA Heater
Aug 27, 2009 | Heating & Cooling
Jun 20, 2009 | York Furnace Draft Inducer Blower Fasco #...
1,256 people viewed this question
Usually answered in minutes!