Question about Weather King 10AJA3601AH Air Conditioner
I have 4 codes flashing what is it
If you shut off the power and turn it back on does it start and run? if so, replace you air filter. Odds are the blower is dirty and if it is dirty the secondary heatexchanger is dirty and if you have a/c your a-coil will most likely be a bit dirty too. And it all starts with the ducts, there is only one place the dirt comes from. This causes bad air flow over time and could be causing your problem. But in order to do this have a hvac company come in and clean it. Find someone who does furnace and duct cleanings. I own a heating, cooling and duct cleaning business and see this all the time. a way to check the air flow is to take the return tempature and the plenum tempature. if the unit is running on high it prob should be around 70-75F diff. The sticker inside the furnace will tell you the proper temp rise.
Now if the rool out switch on the side of the burner box is tripped call a tech and have them check the heat exchanger. a burner tube is most likley gone, but this is very unlikely.
Let me know what you find...
Posted on Jan 22, 2009
SOURCE: York, diamond 90 heating issues!
Look at the electrical schematic on the inside cover to the electrical compartment. It should have a list of fault codes. Locate the condesate drain lines (up to three) and remove them and inspect them for debris/blockage. Clean them and flush them with warm water and clorox solution. Make sure that your condensate line is not blocked and that you are getting drainage from the condensate line. The new high efficiency furnaces generate a great deal of condensate water from the burner and it needs to drain properly.
Posted on Jan 29, 2011
Tips for a great answer:
Dec 07, 2013 | Air Conditioners
Dec 06, 2013 | Air Conditioners
Apr 29, 2011 | Air Conditioners
Mar 05, 2011 | Air Conditioners
Jan 28, 2011 | Air Conditioners
Dec 16, 2010 | Air Conditioners
Aug 23, 2010 | Air Conditioners
Aug 27, 2009 | Air Conditioners
Aug 11, 2009 | Air Conditioners
1,198 people viewed this question
Usually answered in minutes!