Question about Reddy R155D Utility Heater
Last time I used it the heater would run a litte bit shut off , a minute later turn back on did that a few times and then blew a big puff of smoke. now plug it in the fan turns on but the burner won't kick on and it shuts back off.
Check your fuel line for cracks and also the air line. Most likely is the CAD flame sensor, easy to change and only 3 bucks or so. Might also want to check all of your filters. Mine was doing the same thing and it was the high heat limit control and the flame sensor.
Posted on Jan 22, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 03, 2015 | Heating & Cooling
Oct 17, 2013 | Dryers
Mar 10, 2012 | Heating & Cooling
Mar 07, 2011 | Dayton (3UG73) Electric Utility Heater
Dec 28, 2010 | Heating & Cooling
Dec 20, 2010 | Heating & Cooling
Aug 09, 2009 | Hayward 100kbtu Pool Or Spa Propane Gas...
Feb 06, 2009 | Carrier Heating & Cooling
86 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: