Question about Heating & Cooling
I have a comfort glow space heater, vent less model cgr18n that will light and burn for a while then goes out . Is the O.D.S pilot assembly the problem?
If the pilot flame does not touch the thermocouple, the heater will do exactly what you describe.
Get a short piece of copper tubing that will fit snugly over the thermocouple and bend the short piece so that it is in the pilot flame.
Posted on Oct 02, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 06, 2014 | Heating & Cooling
Oct 19, 2014 | Heating & Cooling
Nov 12, 2012 | Desa International Blower Glow Warm Wall...
Oct 23, 2011 | Heating & Cooling
Feb 19, 2010 | Desa International GWP20T GLOWARM Wall...
Nov 18, 2009 | Desa International Heating & Cooling
Oct 01, 2009 | Desa International Blower Glow Warm Wall...
Jan 28, 2009 | Rinnai Desa Vent-Free Infrared Gas Heater:...
Dec 04, 2007 | Heating & Cooling
Jan 18, 2017 | Williams Heating & Cooling
550 people viewed this question
Usually answered in minutes!