Question about Pentair Commercial Mega Therm
Brand new pool heater worked fine all summer and then in September it just burned up
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
You must turn on the pump and let water circulate through the pool and the heater before you turn on the heater otherwise you will ruin the heater
Posted on Apr 16, 2009
This is a fan falure code. It can mean the fan has problems (not likley if the fan goes and isn't labored) You have a sensor in your exaust (probally not this if you don't get a good start) The culperet is probally in the negetive pressure sensor. This is a 2-3 inch disc with wires going to the controls and a rubber tube going to the fan. Pull the tube from the fan and make sure the fan fitting is clear (poke with a tooth pic) Be sure their are no kinks in the hose. If the heater is 4 years old the diaprahm could be bad in the pressure sensor. Check the other things first but this is probally your problem. Good luck, hope this helped.
Posted on Jan 26, 2010
This is an ignition flame falure code. Could be you don't have gas getting to the pilot, no spark to ignite the pilot or your ignition is not reading the flame. Sorry to say but it's probally time to get the pool guy out to look at it. Good luck.
Posted on Apr 15, 2010
Tips for a great answer:
Jul 15, 2016 | Pentair Pool & Spa
Mar 05, 2015 | Pentair Mastertemp 250 Natural Gas Pool...
May 30, 2014 | Pentair Mastertemp Heater
Jun 09, 2013 | Pentair Pool & Spa
Sep 11, 2011 | Pentair Mastertemp Pool & Spa Heater Dual...
Aug 20, 2011 | Pentair Intellitouch Pool or Spa...
Sep 24, 2010 | Pentair Minimax NT Heater
Aug 24, 2010 | Pentair MASTER TEMP HEATER 400 000 BTU NG...
Oct 11, 2009 | Pentair MASTER TEMP HEATER 400 000 BTU NG...
Jun 08, 2009 | Pentair PUREX MINIMAX HEATER; THERMOSTAT,...
24 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: