Question about Carrier Heating & Cooling
The motor inducer keeps running but no flame
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
try checking the pressure sensing switch,it has a tube that should run somewhere close to the inducer fan.sometimes this hose fills with liquids,and makes the units act funny.I don't know if you have a condensing unit or what.the furnace wont try to light if it cant tell the inducer motor is running.any induced draft unit will work this way.you can also do a temp. bypass of the pressure switch to make sure the contacts on it are closing just be sure your inducer fan is running,and you cant leave it like that its just a test.that is a safety feature you really need.
Posted on Mar 19, 2009
ok this is going to sound funny but it seems as though the polarity is reversed going into your furnance. to correct this proiblem you first need to unplug the unit and where the cord goes into the furnance at that connection disconnect the two wires. Once theses are disconnected switch the wires .All you are doing is reversing the way the electricity flows into the circut board. I would wager that is the problem
Posted on Apr 16, 2009
is fan working? if so check the small tube from fan to pressure switch this sometimes will be lose. if fan is working and tube is connected you can check to make sure switch is good by disconnecting hose from fan housing ,start unit **** on hose & hold end so it keeps a vacuum. if everything works than you need to replace fan motor & housing
Posted on Oct 20, 2009
Your doing well just right. When the call for heat is on the draft motor gets a call from the board to come on. When this happens if no voltage is present at the motor then you ahve abad baord. Replace it.
Posted on Nov 28, 2009
Testimonial: "Very professional with positive feedback. Thanks for the help! "
Tips for a great answer:
Jan 23, 2016 | Heating & Cooling
Mar 02, 2015 | Heating & Cooling
Feb 19, 2013 | Heating & Cooling
Dec 27, 2010 | Goodman Heating & Cooling
Dec 10, 2010 | Goodman GMS80903BNA Heater
EACH OF THE FOLLOWING STATUS CODES IS A TWO DIGIT NUMBER WITH THE FIRST
DIGIT DETERMINED BY THE NUMBER OF SHORT FLASHES AND THE SECOND DIGIT BY
THE NUMBER OF LONG FLASHES.
11 NO PREVIOUS CODE - Stored status code is erased automatically after 72
hours. On RED LED boards stored status codes can also be erased when power
(115 VAC or 24 VAC) to control is interrupted.
12 BLOWER ON AFTER POWER UP (115 VAC or 24 VAC) -Blower runs for 90
seconds, if unit is powered up during a call for heat (R-W closed) or R-W opens
during blower on-delay.
13 LIMIT CIRCUIT LOCKOUT - Lockout occurs if the limit or flame rollout switch is
open longer than 3 minutes.
- Control will auto reset after three hours. - Refer to #33.
14 IGNITION LOCKOUT - Control will auto-reset after three hours. Refer to #34.
21 GAS HEATING LOCKOUT - Control will NOT auto reset.
Check for: - Mis-wired gas valve -Defective control (valve relay)
22 ABNORMAL FLAME-PROVING SIGNAL - Flame is proved while gas valve is
de-energized. Inducer will run until fault is cleared. Check for:
- Leaky gas valve - Stuck-open gas valve
23 PRESSURE SWITCH DID NOT OPEN Check for:
- Obstructed pressure tubing. - Pressure switch stuck closed.
24 SECONDARY VOLTAGE FUSE IS OPEN Check for:
- Short circuit in secondary voltage (24VAC) wiring.
31 PRESSURE SWITCH DID NOT CLOSE OR REOPENED - If open longer than
five minutes, inducer shuts off for 15 minutes before retry. Check for:
- Excessive wind - Proper vent sizing - Defective inducer motor
- Low inducer voltage (115VAC) - Defective pressure switch
- Inadequate combustion air supply - Restricted vent
- Disconnected or obstructed pressure tubing
- Low inlet gas pressure (if LGPS used)
If it opens during blower on-delay period, blower will come on for the selected
33 LIMIT CIRCUIT FAULT - Indicates a limit, or flame rollout is open. Blower will
run for 4 minutes or until open switch remakes whichever is longer. If open
longer than 3 minutes, code changes to lockout #13. If open less than 3 minutes
status code #33 continues to flash until blower shuts off. Flame rollout switch
requires manual reset. Check for: - Restricted vent
- Proper vent sizing - Loose blower wheel - Excessive wind
- Dirty filter or restricted duct system.
- Defective blower motor or capacitor. - Defective switch or connections.
- Inadequate combustion air supply (Flame Roll-out Switch open).
34 IGNITION PROVING FAILURE - Control will try three more times before lockout
#14 occurs. If flame signal lost during blower on-delay period, blower will come
on for the selected blower off-delay. Check for: - Control ground continuity
- Flame sensor must not be grounded
- Oxide buildup on flame sensor (clean with fine steel wool).
- Proper flame sense microamps (.5 microamps D.C. min., 4.0 - 6.0 nominal).
- Gas valve defective or gas valve turned off - Manual valve shut-off
- Defective Hot Surface Ignitor
- Low inlet gas pressure
- Inadequate flame carryover or rough ignition
- Green/Yellow wire MUST be connected to furnace sheet metal
45 CONTROL CIRCUITRY LOCKOUT Auto-reset after one hour lockout due to;
- Gas valve relay stuck open - Flame sense circuit failure
- Software check error
Reset power to clear lockout. Replace control if status code repeats.
If status code recall is needed, briefly remove then reconnect one main limit wire to display
stored status code. On RED LED boards do not remove power or blower door before initiating
status code recall. After one status code recall is completed component test will occur.
Thanks for Choosing FixYa.
Oct 05, 2010 | Heating & Cooling
Dec 12, 2009 | Heating & Cooling
Dec 08, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Oct 07, 2009 | Goodman Heating & Cooling
Mar 11, 2009 | Heating & Cooling
63 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: