Question about Heating & Cooling
Hi, I just finished installing a Senville Mini Split HVAC unit. After evacuating the lines, I opened the valves on the outside unit, and turned on power. (The outside unit was supposed to be shipped with enough R410a to run the unit, with the lines supplied.) I didn't hear a great deal of hissing noise when I opened the line valves, so it could be low on R410a, but??? It shows an error code of E4, but there is no documentation with it to tell me what that code means. The compressor does not function on either heat or cool, but the blower does work on fan only mode. All the settings seem to turn on the correct lights on the panel, but it has this error code posted. Can anyone tell me what that code means? I suspect it's telling me it's low on R410a, but...
The model is: KFR-35GWZ/BM
Thanks in advance...
Corley I got the same error code E4 with KFR-50GWZ/BM, but no where in manual which mentions this. I could not find from their Website http://gt-world.com/product_info.php?products_id=34
Will have to call them tomorrow. Has anybody gotten the solution yet? thnx.
Thanks for your question, you will need a set of gauges on the unit to determine if the unit came precharged, if it didn't then you will need to vacuum down the unit, at least three times, after each time release a little 410a into the system them evacuate again, 410a is bad for drawing moisture, did you put an in-line filter dryer on as well ? after you find out about the freon level, then look at the name plate rating for amount of 410a needed, before adding the freon, use nitrogen to leak check the system, then weigh in the proper amount of 410a, unit should run really well after that, hope that helped, thanks again for your question, please feel free to come back if you have any more questions, thanks, mr.grzz
Posted on Jan 21, 2009
SOURCE: Senville Mini Split Error Code
The E4 light on your system is saying there is a commiuntion problem between the inside unit and the outside heatpump unit.Make sure there are no loose wires and you wired it properly,The S wire is the commiuntion link wire make sure it is a solid run between both units.I had the same problem with my system and it was the s wire not making a good connection.
Posted on Apr 25, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 29, 2016 | Inverter Heating & Cooling
Sep 08, 2015 | Senville 24000 BTU Energy Star Ductless...
Jul 02, 2015 | Senville 24000 BTU Energy Star Ductless...
Dec 31, 2014 | Senville 18000Btu 21 Seer 12.5 EER...
Jul 26, 2014 | Samsung AQV12VBCN Vivace Mirror Finish...
Aug 24, 2013 | Heating & Cooling
Aug 22, 2013 | Senville 18000 BTU Energy Star Ductless...
Nov 03, 2008 | Heating & Cooling
970 people viewed this question
Usually answered in minutes!