Question about Leviton 003-1755-W Three Rocker Switches
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
I don't understand your problem. Green wire is ground goes to the yoke. it should not have any current on it If it does sumbody messed up real bad!
a combo outlet/switch has three brass screws and one nickel screw. yoke should have a green hexagonal screw.
Posted on Oct 25, 2009
SOURCE: Leviton Dimmer Switch wiring and
I recently purchased a Leviton Dimmer switch which has a brown lead. This switch is to replace 1 of 2, 3 way switches that control the ceiling light in my kitchen. My problem is the new dimmer switch has 4 leads including a brown one which has me confused. I have installed and replaced numerous dimmer switches without difficulty. Please help.
Posted on May 20, 2010
SOURCE: We are replacing an old
Leviton T5625 has shutter (tamper resistant) mechanism that blocks access to the contacts unless a two-prong plug is inserted. My understanding is this mechanism prevents child from sticking piece of metal into receptacle and getting shocked. Tamper resistant receptacles are code for new home construction, and receptacle is marked with TR. The light switch part of device works at all times, with or without two-prong plug in receptacle.
Electricians test, they don't guess.
Let's test your wires using ordinary two-prong tester.
Tape wood sticks to tester leads to keep hands away from power. Stand on dry surface or wood boards. Do not shake or sweat.
Separate wires for testing
Turn power ON.
Test each wire to bare ground wire.
Tester lights up on Hot wire. Hot wire connects to either dark-colored screw, as long as there is a brass connector plate that connects both dark colored screws. If connector plate is missing, add a jumper wire between both dark screws so they are connected together.
Hot wire is identified.
Now test Hot wire to each other wire, except bare ground wire.
Tester lights up on neutral wire. Neutral wire connects to silver screw.
If neutral wire is white wire, AND both white wires were connected together before, then they both connect to silver screw.
The last wire is the Load wire that goes to fan, light, motor. Load wire connects to brass colored screw.
Double check instructions with instructions on new device.
Add a comment any time.
You can also take advantage of fixya phone service.
For a price, fixya expert speaks to you over the phone while you test and wire the device.
Posted on Dec 29, 2010
Tips for a great answer:
Nov 12, 2014 | Leviton 23351 T8 Or T12 Turn-type...
Oct 05, 2012 | Electrical Supplies
Sep 01, 2011 | Leviton 112-05604-2WS 15A 4-Way Decora...
Jun 03, 2011 | Leviton 3W Lighted Toggle Switch -...
Dec 22, 2010 | Leviton Decora Light Dimmer Switch
Sep 30, 2010 | Leviton Electrical Supplies
Nov 22, 2009 | Leviton (102-5G108-RW5)
Oct 10, 2009 | Leviton Decora Light Dimmer Switch
Sep 26, 2009 | Leviton 5225ISP Switch and Outlet
Sep 23, 2009 | Leviton 6124H-A 6124H-A Decora LCD Timer...
Feb 19, 2012 | Leviton 003-1755-W Three Rocker Switches
65 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: