Question about Honeywell TH4210D1005 Heater
I have heater set to 72 after it warms to 72 blower continues to blow but cool air once temp goes below 72 it starts to blow hot air again
Sounds like either a short between the G and R t stat wires or the relay in the control board is faulty. Easy way to check is remove the G wire from G terminal on the control board, if the blower stops, there is a short in tje t-stat wiring, if it continues to run a new control board will be needed since the relay is part of the board.
Posted on Jan 08, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
On heat pumps, the normal setting is simply an air conditioner working in reverse. The EMT or AUX heat is a supplemental heating system using electric heating elements instead of the hermetic (compressor) system. As far as why the regular heat does not work it can be one of many things. low freon charge. reversing valve not functioning. The defrost cycle not working. Take your pick. you may want to call a service man to repair it as the electric (EMT) is not as efficient.
Posted on Nov 04, 2007
SOURCE: Honeywell RTH230B a/c problem
if you set the thermostat on 70 and your house won't get ant cooler than 72, there is a problem with your system,not your stat. I'm thinking you are low on refrigerant if it is somewhat working. when the unit is running, if you can get your hand on the larger refrigerant line under the black insulation, it should be cold, about 55 degrees.
Posted on Jun 19, 2009
If unit worked before you tryed changing t-stat then its possible the t-stat wires are shorting each other out.take t-stat back off cut back wires a good 6 to 10 inches or if you dont have that much wire to play with just cut back as far as you can and make sure there is no bare wire touching each other ,then just to test unit to make sure its working ok twist yell.,red,green together this should bring both units on and should blow cold.if this works up to this point on the new stat read directions closely there might be a jumper wire in the stat that needs connected usually from y1 to w1 you would install a jumper wire .see if this helps if not write back i have 1 other solution.i hope this helps
Posted on Sep 15, 2009
You can make sure it is not the thermostat by crossing or jumping the R and W terminals (or associated wires) together. This will keep the furnace calling for heat. As it is approaching set temperature, get in front of the furnace and inspect the air filter to make sure it is clean, watch the control module for any error codes that may be turning off the system prematurely.
On a call for heat, the 24 volt thermostat sends a signal to the control module. The control module will indicate a call for heat with a light on the control either blinking or remain solid depending upon model. The inducer (exhaust) blower will purge all gasses from the furnace and pressurize a pressure switch. Once the pressure switch tells the module to continue, the electronic ignition will energize and send 120 volts to the igniter. The igniter will glow and you will be able to see it if viewed thru the small inspection port. Once the igniter gets hot enough, it sends a signal to the module opening up the gas valve (24 volts). Either a pilot will come on or the burner tube will ignite then spread the flame to all burners. Lastly a safety sensor will be looking for a certain temperature within a few seconds and the furnace will continue to operate and the room air blower will turn on in a minute or two.
What could go wrong? The unit will not run if there is no signal from the thermostat (bad thermostat or broken wire), the control module does not sense a signal from the thermostat (bad control), the inducer does not energize (bad motor), the pressure switch does not close (blocked vent piping, bad switch, plugged condensate hose), the igniter does not energize (bad control, bad igniter), the gas valve does not open or there is no gas (bad gas valve, broken wire, no gas), the pilot does not light (dirty pilot), the burner does not light (bad burner, plugged orifice, not enough combustion air), the flame does not spread to each burner (bad flame spreader, dirty flame spreader, more bad burners), the flame safety sensor does not detect flame (dirty or bad flame spreader, bad flame sensor, broken wire, bad control), or the room air blower does not energize (bad fan motor, bad control).
Posted on Mar 07, 2010
Tips for a great answer:
Jan 28, 2014 | 2004 Ford F150
Feb 09, 2013 | 2000 Pontiac Grand Prix
troubleshoot this types of problem,click the link below :---
Car heater blowing warm, but not hot air?http://schematicsdiagram.blogspot.com/2011/12/car-heater-blowing-warm-but-not-hot-air.html
Engine Overheats and heater blowing cold?
Heat blows cold on drivers side and hot on passenger side?
No heat on car? http://technoanswers.blogspot.in/2012/02/no-heat-on-oldsmobile-silhouette.html
Heater blows intermittently and temp gauge goes erratic?
Heater blows cold?
Heater/AC blower motor not working?
A/C, heater, defroster fan, not working? http://technoanswers.blogspot.in/2012/02/ac-heater-defroster-fan-not-working.html Heater problem?
This will help.Thanks.
Mar 27, 2012 | 1994 Volvo 960
Jan 18, 2011 | Heating & Cooling
Jan 15, 2010 | Heating & Cooling
Jun 17, 2009 | 2000 Mercedes-Benz CLK
Jun 09, 2009 | Coleman Propane Forced Air Heater...
Feb 20, 2009 | EdgeStar Portable Air Conditioner Heater
Nov 24, 2008 | Goodman GMS90703BXA Heater
158 people viewed this question
Usually answered in minutes!