Question about Cooper Wiring Devices ACE6003W-K ACE" 3-WAY ROTARY PUSH DIMMER
I changed an old brass switch for a new plastic one and changed it wire for wire may of caught a nuetral with screw driver when changing
That could be the culprit - right there.
You see, the new dimmers work electronically. There are no moving parts really. Voltages are changed in some very high tech ways thru transistors and triacs. These are comparatively "delicate" devices to the old snap switch and rotary dimmers that had large moving pieces that could handle a large load (like your short via the screw driver) for a short time. Not so with a transistor or triac however. There are so small, they have no way to dissipate heat like the other switches and *instantly* fail. The amount of current in amps needed to blow the transistor or triac is much lower than that needed to blow a fuse or circuit breaker - so that's why it never opened. That is why the instructions often call for removing power at the panel before installing.
So, unless it is a simple wiring error, my money is on a blown dimmer switch. Double check you work and try again with the power OFF.
Posted on Jan 16, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
I think your goal with the 2 way switch is to be able to turn the landing light on/off from either the top of the steps or the bottom of the steps. When you run a one way light in with that circuit it will not make a complete circuit, hence the 2 way will not work. If your bathroom switch was in with the light switch at the top of the steps, you will have to seperate these two switches. Make the bathroom a switch by itself, and then connect the two way switches. If a circuit is not making a loop it will not work. 2 ways must make an uninterrupted loop, (the one way is interrupting the loop) in order to function properly. Hope this helps!!!
Posted on Sep 21, 2010
Tips for a great answer:
Mar 14, 2015 | Electrical Supplies
Nov 19, 2011 | Home
Dec 12, 2010 | Leviton White 3-way Toggle Switch 15a...
Oct 17, 2010 | Broan-NuTone Broan 68W White Decorator...
Oct 17, 2010 | Broan-NuTone Broan 68W Dual Rocker Switch
Oct 01, 2010 | Home
Sep 21, 2010 | Cooper Wiring Devices ACE6003W-K ACE"...
Feb 14, 2010 | Cooper Industries Cooper Wiring 2158V 3...
Feb 08, 2010 | Dryers
Aug 10, 2008 | Dryers
72 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: