Question about Heating & Cooling
I can't tell if it's igniting, I assume it's gas powered, can you hear the main burner light? or see the pilot light at all? If you answered yes to either, then I'd say it's the safety cut out, not having enough time to heat the sensor. See if there is a way of holding it in the start position for say 30 seconds, then release, if not then ask repair man if there is a way of adjusting the starting hold-on time, hope this helps...
Posted on Jan 08, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: I'm a new plumber. I
1. You need to fill the entire system with water before you fire it,
boiler AND radiators... Then, you would normally vent as much of the
trapped air in the system as you could... It's not like you are only
going to fill just the boiler and then pump that water through the
There is a temp setting on the boiler, but I don't think that's a solution. Remember that the water in the system is going to begin circulating as soon as you start the boiler. So, it will start circulating when it's cold, and then gradually warm up.
Your problem is not the sudden rush of hot water, it's going to be filling the system in the first place, and getting the boiler started before the system freezes up ...
I don't really have any suggestions for you though, other than perhaps renting one of those construction heaters ... and bring the building temp up a bit. But there's certain dangers associated with them too... Carbon Monoxide for one, fire is another (if used improperly).
Just thought of something: Fill the system with glycol based anti-freeze solution that's designed for heating systems. That oughta do it...
I'm guessing there's not a functioning water heater either at this point, is there ? If there was, you could possibly rig something up to fill the system with lukewarm water, and fire it before it freezes up.
2. You don't have a lot of choice. You have to fill the system, fire the boiler & wait.
It is going to take a long time to get the system up to temperature. Instant circulation is a double edged sword. The upside is you get a little bit of heat into the water & have it moving making freezing less likely. The downside is, it's hard on the boiler with that much cold water coming back you are likely to have condensation.
Posted on Apr 22, 2009
Tips for a great answer:
Feb 25, 2017 | Water Heaters
Feb 13, 2015 | Water Heaters
Aug 14, 2017 | Honeywell Programmable Thermostat Heater
Dec 27, 2013 | YouTube Videos
Aug 29, 2011 | Heating & Cooling
Jan 05, 2011 | Heating & Cooling
Dec 09, 2010 | Rheem Water Heaters
Jun 06, 2009 | Combi Centre DX - Mango
May 15, 2009 | Water Heaters
Apr 22, 2009 | Heating & Cooling
Oct 20, 2017 | Heating & Cooling
28 people viewed this question
Usually answered in minutes!