Question about Heating & Cooling
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
E39 Fault is thermister, Mitsubishi way of saying im not going to start because there is something wrong. Generlly it is compressor fault or short of gas. Im guessing if you turned the power out. Waited twenty seconds, turn it back on. Now if you go to the outdoor part. Wait exactly 3 mins. If you hear the compressor try to start and fail then it would more then likely be your compressor if you dont hear anything and the unit faults out it will either be a board or short of gas.
Either way If the unit is under five years old get a warrenty agent out to look at it.
Sorry I couldnt tell you for sure but MHI are very vague when it comes to fault codes
Posted on Mar 05, 2009
SOURCE: LG split (3 indoor) LMU360CE
The LED #2 is only flashing while in disconnection or short in Thermistor (3 sec off / 0.5 sec on). If you want to change it, note: this is not an easy job to do! You will need to remove the top panel, then remove the control paneland then the front panel to gain access to the thermistor. The part isnot available to the public and requires an authorized service techfrom LG to take care of this problem. You will need a special tool toremove the front door seal spring clamp.
But you can call customer service @ 800 243 000 and see if theycan transfer you over to parts. Just give them the model and serial #and see if they would be willing to sell you the thermistor part. Youwill also need the door seal spring clamp removal tool to make the jobeasier.
Posted on Aug 02, 2009
Sounds like an interconnecting wiring error. Check wiring connection i.e. wires are connected in right order 1 to1 2 to 2 etc. from indoor terminal board to outdoor terminal board. Also check for slack or loose connections.
Hope this helps I take the time to answer your question so please rate me
Posted on Jun 28, 2010
E-5 -Comms Error, check your wiring, remove external pumps. Split/Multi - check volts from terminal N to 3 = 0 - 65 Vdc, Multi V - 4 Vdc terminals 3 and 4
Posted on Jan 03, 2011
Tips for a great answer:
Oct 13, 2017 | Panasonic Heating & Cooling
Apr 19, 2017 | Samsung Heating & Cooling
Dec 05, 2015 | Heating & Cooling
Mar 29, 2015 | Refrigerators
May 04, 2013 | Daikin RXYMQ48MVJU, VRV-S Air Cooled Eight...
Aug 23, 2011 | Samsung Heating & Cooling
Jan 19, 2011 | Heating & Cooling
Apr 17, 2010 | LG LS-L1210CL Mini Split Air Conditioner
• Wrong or missing wiring between indoor and outdoor unit cable
• Defect of communication components in indoor pcb assembly
• Defect of communication components in outdoor pcb assembly
• Defect of power supply components in outdoor pcb assembly
• No ground connection in air conditioner unit
(affected by noise in power source)
Jun 30, 2009 | LG Heating & Cooling
26 people viewed this question
Usually answered in minutes!