Question about Intermatic T104M 208-277Volt 40-amp Timer Switch-Double Pole / Single Throw
Copy following links:
Posted on Oct 13, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: need plain install instructions
Let me see if I can help
Power coming in from the live circuit ( Main Power ) needs to connect to The A Terminal and #1 Terminal and the ground point.
Power connection out to the equipment you want times connects to the A terminal and then the #2 Terminal and then the same ground point.
The #1 and #2 Terminals are your break point switch, so when the timer is one power is applied to the #2 terminal, when off, no power to the #2 terminal.
Hope that helps some.
Posted on Mar 24, 2009
john, i'm assuming the water heater is 240 volts and the timer is 240 volts, if ok follow these instructions. the 2 wires coming from the breaker box goes on 1 & 3 screws, also each yellow wire going to the timer motor goes on 1 & 3. now the 2 wires going to the water heater goes on 2 & 4. be sure to ground the timer box
Posted on Apr 13, 2009
SOURCE: i am installing an intermatic
Add a comment and provide more information.
A lot of factors need to be narrowed down.
Did everything work fine before connecting fireman burn-out protection switch?
What happens when you disconnect switch?
Is the timer rotating?
Does the manual override work?
Is this a new installation?
This sounds like a dual T-104 pool timer that controls more than the heater, what else is controlled, and do the other Loads work correctly?
Posted on Nov 19, 2010
Tips for a great answer:
May 15, 2013 | Pool & Spa
Jul 20, 2012 | Intermatic T21004R- Pool-Spa Mechanical...
Jun 23, 2012 | Intermatic T104 24h 208-277v Mechanical...
Sep 11, 2011 | Intermatic Timer T12404R Pool & Spa...
Jun 14, 2011 | Intermatic Timer T12404R Pool & Spa...
May 21, 2011 | Intermatic T40404R - Pool-Spa Control...
Nov 19, 2010 | Intermatic HEATER DELAY SHUT OFF SWITCH...
Sep 26, 2010 | Intermatic T104 24h 208-277v Mechanical...
Jun 27, 2009 | Intermatic T104M 208-277Volt 40-amp Timer...
Apr 13, 2009 | Intermatic & Indoor/Outdoor Rain Tight...
38 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: