Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
The limit switch on the inducer has tripped. There are two wires that go to a small disk about the size of dime that has a small button in the center. Push this little button and you will feel a littl snap and the unit should fire up. Check all the manual reset limits as well. If the unit still won't start, jump the two wires by bypassing the limit switch. If it starts, then replace the switch. Bypassing the switch is only temporary and could lead to death if it is used as a permenant fix.
Posted on Apr 03, 2009
ok this is going to sound funny but it seems as though the polarity is reversed going into your furnance. to correct this proiblem you first need to unplug the unit and where the cord goes into the furnance at that connection disconnect the two wires. Once theses are disconnected switch the wires .All you are doing is reversing the way the electricity flows into the circut board. I would wager that is the problem
Posted on Apr 16, 2009
Your doing well just right. When the call for heat is on the draft motor gets a call from the board to come on. When this happens if no voltage is present at the motor then you ahve abad baord. Replace it.
Posted on Nov 28, 2009
Testimonial: "Very professional with positive feedback. Thanks for the help! "
The anticipator basically prolongs or reduces the time from shut down to start up, so your furnace or air conditioner isn't cycling too much , off and on. It also will anticipate that the setting you have the thermostat set at is near, and will shut thermostat/burner off early, assuming that the temperature will be reached soon, just from heat already in chamber being circulated through system. If it gets too cold before furnace turns on, adjust anticipator, if too hot when it shuts down, go the other way, but whenever you move it, just go a little at a time, until you get it where you want it.
Posted on Mar 13, 2010
Testimonial: "Thanks for the explanation about anticipators. Do they figure much in furnace problems?"
Tips for a great answer:
Nov 27, 2016 | Heating & Cooling
Jan 24, 2014 | Fedders Heating & Cooling
Nov 16, 2013 | Coleman York Control Board 03101237000...
Mar 03, 2013 | Omega Trane Furnace Draft Inducer Blower...
Feb 18, 2013 | Goodman Furnace Draft Inducer Blower ...
Jan 25, 2013 | Coleman 7990-319p Evcon Gas Furnace...
Oct 29, 2010 | Electric Circuit Breaker Kit for Furnace
Feb 06, 2010 | York Furnace Draft Inducer Blower Fasco #...
Jan 02, 2010 | Coleman Propane Forced Air Heater...
Oct 25, 2008 | Heating & Cooling
Sep 25, 2017 | Heating & Cooling
81 people viewed this question
Usually answered in minutes!