Question about Heating & Cooling
Gas log lights correctly then shortly will shut down, pilot and all. You can relight immediately, and will run for a few more minutes then shut off again.
After you relight have you tried to leave the gas valve on pilot for 10 to 15 minutes so the themolpile warms up enough to send mil-volt signal. you also have a thermocouple that senses flam so if the flame is not hitting that just wright it will shut off. Is this fire place ran off a thermostat or a on off switch. If you are running off a thermostat then i would try to find on/off switch and try that. You might have to change pilot assembly out.If you do this and don't have manual i would take a picture of the log set up so you put it back together. Make sure all connections are tight when you go back together
Posted on Jan 20, 2009
Sounds like the gas regulator has failed.
There will be sufficient gas flow to light the pilot and get a flame prove, then the main burner lights, you will probably see the pilot flame reduce somewhat, and no longer fully surround the flame prove sensor.
When the unit is relighted, the complete sequence starts all over again.
Have the gas regulator checked and adjusted (if adjustable) or replaced by a qualified technician.
Posted on Jan 20, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 08, 2014 | Emberglow Melbourne Oak 24 in. Vent-Free...
Dec 04, 2013 | Water Water Heaters
Nov 26, 2013 | Woodland Direct CD Vent Free Gas Log Set...
Dec 23, 2012 | Hayward H Series Pool & Spa Heater 400k...
Mar 31, 2012 | Water Heaters
May 14, 2011 | Kenmore 500 6952 Dryer
Jan 07, 2010 | Desa International Unvented Gas Space...
Dec 11, 2009 | Desa International CCL3018N 18KBTU VNTFRE...
Oct 18, 2008 | Imperial IFS40 Deep Fryer
789 people viewed this question
Usually answered in minutes!