Question about Heating & Cooling
Well you have a old furnace which is hard to light ,so here goes there is a round plate on the front above the gas valve about 8inches up remove this plate ,there may be a second plate ? you need to look down to the burner to see the pilot (alight we help you see it ) A flexable BBU light in needed so you can get it to light the pilot not easy but this way works .
Posted on Jan 08, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
When a pilot lite habitually goes out the thermocople has failed. The are pretty cheap. If you remove yours and go to a local applicane parts center they can provide you with one the same lenght as your current one for a much cheaper price than a plumbing and heating source. In the process of changing the thermocouple when you disconnect it from the gas control valve take a Q-tip and clean the mating area as best you can. You can try cleaning that mating area before changing the thermocouple first. You might just get lucky and not have to buy a new one.
This is not a hard task. It is a bit tedious to get to the area near the flame head but I am pretty sure you can do this. Just make sure the new thermocople is positioned like the one you removed.
There is a very very remote possibility that the gas control itself is failing but I doubt it. You still would have to change the thermocouple first in order to troubleshoot.
Thanks for using FixYa.
Posted on Mar 27, 2010
There is a wind shield for this unit, call 502-589-5380 and ask for a drawing for the wind shield and have it made out of 26 gauge sheet metal.
Posted on Dec 15, 2010
Tips for a great answer:
Oct 07, 2014 | Coleman 7990-319p Evcon Gas Furnace...
on Mar 20, 2010 | Heating & Cooling
Mar 09, 2014 | Heating & Cooling
May 14, 2011 | Ruud Heating & Cooling
Feb 28, 2011 | Heating & Cooling
Feb 05, 2011 | Heating & Cooling
Jan 01, 2009 | Heating & Cooling
Oct 17, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
397 people viewed this question
Usually answered in minutes!