Question about Williams 1403622 Gas Compact Heater
New Wall Furnace. I connected the thermostat and tried lighting the pilot light. Held pilot button in for a minute or more and it still goes out when I release the button. Tried many times. I see thermocouple replacement mentioned many times here on this board but this unit is brand new. Can the wiring I did for the Thermostat have anything to do with it?
Thanks for any help
The low voltage wiring and the thermostat has noting to do with the pilot function of the wall furnace, check to see if when you have the pilot lit manually, while holding the button in does the flame impinge on the thermocouple and does the flame try to wrap around the thermocouple? if not the thermocouple and pilot flame need to be adjusted so that it impinges on the TC, if it does have a good flame impingment, then you probably have a bad TC from the factory, call them and have them send you a new one if still under warrenty.
Posted on Jan 20, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 03, 2016 | Heating & Cooling
Dec 08, 2015 | Williams Heating & Cooling
Feb 11, 2015 | Cozy Heating & Cooling
Nov 19, 2014 | Heating & Cooling
Mar 21, 2014 | Heating & Cooling
Oct 21, 2013 | Omega Trane Furnace Draft Inducer Blower...
Jan 13, 2012 | Heating & Cooling
Oct 30, 2011 | Empire DV-35 Heater
May 06, 2011 | Heating & Cooling
Jan 23, 2011 | Heating & Cooling
856 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: