Question about Goodman Manufacturing Heating & Cooling
Fan works but does not always comes on when unit comes on in either a/c or heat
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
the fan is controlled by a fan center or a stack switch. as burners light and heat up the spring sensor on the bulkhead above burners heats up and turns and a a point energizes the indoor fan if it gets to hot the burners go out on safty. sounds like a fan control is bad tap on them gently and they sometimes break loose but if not then have a pro replace fan control and test heat exchanger.
Posted on Oct 24, 2008
If this old unit has a outside transformer then you will need to shut off the breaker and take the wires off the compressor and tape them up. Then turn the breaker back on and it should run.
Posted on Jan 03, 2010
Sounds like there may be a separate thermostat to run the fan when the temp in attic reaches a certain point, this can be disabled
Posted on Jun 22, 2011
Tips for a great answer:
Nov 01, 2015 | Heating & Cooling
Sep 04, 2014 | Heating & Cooling
Aug 05, 2010 | Heating & Cooling
Dec 29, 2009 | Heating & Cooling
Sep 22, 2009 | Heating & Cooling
May 18, 2009 | Coleman Mach III Air Conditioner
Jun 17, 2017 | Heating & Cooling
Dec 06, 2008 | Heating & Cooling
Oct 24, 2008 | Ruud UBHC Air Conditioner
Jan 05, 2016 | Goodman Manufacturing Goodman MSG18HRN1...
65 people viewed this question
Usually answered in minutes!