Question about Electrical Supplies
Briggs 14.5 horsepower generac
Posted by Anonymous on
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
I am assuming the generator worked fine before the oil change. Now that you have done the oil change the genset does not start. These generators have a safety switch, which is basically an oil pressure switch that keeps the engine from running when there is not enough oil in the engine. Make sure that there is enough oil and if there is, look for a wire that runs along side of the engine to a round component. disconnect that wire and try starting. If it does not start then try to ground out the wire to the engine block. If this does not work, then there is other engine problems.
Posted on May 08, 2009
Hello, I would not advise you to adjust the speed without a frequency meter. for 220 volt operation, you will have to use the twist - lock receptacles and not use the neutral in the receptacle. This means one of the generator's hot leads is going to be the neutral in your system. The frame of the generator may be connected to the neutral of the generator, so be careful so that you do not receive an electrical shock. The voltage is adjusted within the receptacle box. There might be a small hole on the right side of the receptacle box that you can insert a small blade screwdriver into to make the voltage adjustment. You do not need to change this much to change the voltage. Now, the frequency is adjusted by a self-locking nut located under the air cleaner right side, when facing the engine. There is a spring on this nut / bolt assembly. I think it is a 5/16 nutdriver or socket that you need for this. Turn counter clockwise 1/8 of a turn. This will slow down the generator to about 50 - 55 hz. This is okay if you are running at around 52 hz. As the generator loads, the rpm will drop down. A frequency meter would be great to use here, as a too low rpm could burn out electrical motors and other equipment that you are using. Feel free to contact me firstname.lastname@example.org www.freelancemissions.com
Posted on Jan 22, 2011
Testimonial: "Thank you for the quick response. Great advice and outstanding instructions."
Tips for a great answer:
Jun 28, 2016 | Generac Electrical Supplies
Dec 07, 2015 | Briggs & Stratton Power Products 5,550...
Sep 10, 2015 | Briggs Electrical Supplies
Feb 16, 2018 | Generac Electrical Supplies
Aug 07, 2013 | Swisher T14560 T - 60" Trailmower with 14...
Nov 09, 2012 | Swisher T14560 T - 60" Trailmower with 14...
Aug 14, 2012 | Swisher T14560 T - 60" Trailmower with 14...
120 people viewed this question
Usually answered in minutes!