Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Split System Air conditioner
There normally two types of leakages from the wall unit.
1.The warm air in the room when comes in contact with the cooling coil of heat exchanger (consisting of fine fins where compressed refrigerant evaporates) looses its heat & cannot retain the same moisture content at lower temperature at the point of contact with evaporator. There is a provision of a drain pipe to carry this condensed water to outside water drain. So if the drain pipe is choked or the coupling joint of the drain pipe at the bottom of cooling coil is not proper, there will be water leakage, This can be easily attended by physically looking at the fittings.
2.The second problem can be the leakage of the refrigerant. If there is second type of problem, then there will be very little or no cooling irrespective of continuous running of air conditioner. This can be easily checked by feeling the temperature of outlet air from the air conditioner.
Conclusion-As you have written that there is leakage from the air conditioner, but you have not written whether it is visible or invisible. If the leakage is visible, it is problem number 1 & if it is invisible, it is problem number 2.
If you are not satisfied you are free to ask for more explanations.
Posted on Jan 29, 2008
if no cold blowing,evaporator is not working,have you ever heard compressor is running,check this out,no compression of course you dont have cool on evaporator.if the compressor is running check the oprating current,if still have enough freon charge,if not running check thermostat reset setting on the coldest,ifn still not run check overload relay on panel control reset lever to put back compressor to run,check condensing fan if working,if not check also over load protection,this should be done by ac tech nician.have a nice day,dont gorget to rate me, thank's
Posted on Apr 18, 2009
The simplest way of explaining this is as per the following. On your outdoor compressor unit there should be two pipes, one smaller diameter [high pressure] and a larger diameter pipe [low pressure]. Turn your A/C on inside the house and then shut off the smaller diameter pipe. Run the unit for a around 3 to 4 minutes and then check if the cooling is reducing from the unit inside the house. When you feel room temperature air [not cool] being emitted from the indoor unit shut off the larger diameter pipe and turn off unit. Isolate electrics, disconnect A/C piping and immediately seal the piping with good quality tape to prevent egress of dirt. When re-installing a quick purge of gas is usually only required to clear the lines if they were sealed properly and kept clean. Ideally running a vacuum pump is recommended but if care was taken then it may not be needed, as in many of my installations.
Posted on Nov 13, 2009
5 flashing is ' compressor drive' and check the high pressure, condenser fan motor capacitor for proper running
Posted on May 21, 2010
Tips for a great answer:
Mar 03, 2015 | Fujitsu Heating & Cooling
Dec 22, 2009 | Fujitsu 24C1 Air Conditioner
Aug 07, 2009 | Fujitsu Heating & Cooling
Dec 30, 2008 | Fujitsu 24C1 Air Conditioner
Sep 12, 2008 | Fujitsu 18C1 Air Conditioner
45 people viewed this question
Usually answered in minutes!