Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Coleman Gas Heater for home
I have a Coleman gas heater. My heat won't come on. I can here the blower comming on when I turn on the thermonstat. However no heat will come out. I went up in the attic and the heater instructed me not to light it with a flame. There was a yellow spiral kind of pipe with what look like a little yellow open and close valve. It looked like you should turn it and let the gas come in the heater from the gas line.I wasn't sure if it really was how to turn on the heater. I need some help. should I call the gas company or another company.
Posted on Nov 06, 2008
3 blinks is a pressure switch error clear the hose going to the inducer housing you may need a paper clip to stick into the barb fitting on the motor housing
Posted on Oct 03, 2009
Testimonial: " I took off the tube and inserted a paperclip into both barbed ends. its works great now. You guys saved me at least $100 THANKS!!!!!!"
The chances are that the furnace was running when the power went out. This will cause the high limit switch to cutout and needs to be manually reset.
You will find that switch in the blower compartment near the blower. Usually somewher near the highest point of the cabinet.
Push the little red button firmly till it clicks.
When the power goes out while the furnace is running the heat builds up because the blower shuts down immediately and causes this limit switch to cut out.
If you have a electric tester you can also follow the low voltage circuit till you find the open switch. Ther is usually a wiring schematic on the door cover of most furnaces.
I hope that this will help you to solve your problem!
Thanks for using Fixya!!
Posted on Dec 09, 2009
Check the air filter, condensate drain lines for blockage and vent piping for a build-up of water. If nothing, you will be needing to replace the circuit board (hopefully under warranty).
Posted on Mar 14, 2010
Turn off the power to furnace.
on the last burner to light there is a small metal rod in front of the burner. This is a safety called the flame sensor. It is dirty. Unscrew it from the bar ( 1 Screw) unplug the connector wire from it and clean it with steel wool. it will be kind of burnt. Plut back in place and turn on the furnace to cycle.
Posted on Apr 04, 2010
Tips for a great answer:
Jan 02, 2016 | FACTORY AC PARTS Limit Switch Double Pole...
Dec 16, 2015 | Heating & Cooling
Sep 13, 2014 | Heating & Cooling
Sep 23, 2013 | Rheem Ruud Weather King Corsaire Rheem...
Dec 29, 2010 | Sony BRAVIA KDL-46S2000 46 in. LCD HDTV
Dec 01, 2008 | Heating & Cooling
Sep 07, 2008 | Frigidaire Washing Machines
Jan 10, 2008 | Frigidaire AEQ7000ES Dryer
371 people viewed this question
Usually answered in minutes!