Question about Humidifiers
Was working when the furnace was cleaned.
None leaking? Try removing the cover, and manually cycling on the controler switch? Does the solenoid click on, next to the humidifier (the unit with the water line running through it, with wires coming out of it)? If it does click on, is water running down the water pad? It doesn't necessarily drain water when it's working correctly. All of the water SHOULD be getting evaporated into the air return duct.
If it's clicking on, but no water is running out, you should check the water supply saddle valve and make sure it wasn't turned off during servicing.
If it's not clicking on, you should test that you are getting voltage (12v-18v DC) to the solenoid. If you're not, check all wiring connections and make sure they're tight. If you still don't get power, you have either a problem with your control unit/humidistat, your DC power supply, or the control board on your furnace.
Posted on Jan 06, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
I am having the same problem. I have had my humidifier for about 5 years now and I just started having the problem where the water continuously flows through the solenoid. I took apart the solenoid by removing the fittings from both sides. When I did that, I noticed that there was a hole in the metal that allowed me to see through to the other side. Apparently, it had corroded and and broken through, allowing the water to pass through the solenoid without really going through the valve within the solenoid. There are several sites that sell replacements for about $70, which is not cheap, but cheaper than buing a new humidifier for $120. Here is one site I found: http://www.iaqsource.com/product.php/honeywell/32001639-002/?product=112783&category=1142
Posted on Nov 20, 2008
A simple check you can perform on your aprilaire 760 is the following:
1) locate the two brown wires coming out of the 760 (these wires will be wired to tell the 760 to turn on when the hvac bower is on and the humidistat is calling for moisture).
2) temprarily disconnect the two brown wires from the external wiring and then short the wires together. All you're doing here is bypassing the your thermostat and bower-on indicator.
With the 70 unit plugged in to the wall outlet and the two brown wires connected together, both the fan and the solenoid valve (water inlet valve) should both be activated.
Posted on Dec 29, 2009
sounds like you may have it wired to a continuous power source vs one that shuts off with the furnace. The most common wiring is red to C & white to W
Posted on Jan 13, 2010
Tips for a great answer:
Oct 27, 2013 | Honeywell Power Humidifier: Furnace...
Mar 03, 2010 | Aprilaire 600 Humidifier
Jan 09, 2010 | Honeywell Humidifiers
Jan 08, 2010 | Aprilaire 550 Humidifier
Mar 05, 2009 | General Filters 1042-LH Humidifier
Dec 20, 2008 | Honeywell Power Humidifier: Furnace...
Nov 22, 2008 | Carrier SBP Humidifier
Jan 03, 2008 | Aprilaire 700 Humidifier
74 people viewed this question
Usually answered in minutes!