Question about Intermatic Inc. EJ500C Digital Wall Switch Timer - Self-Adjusting Feature
Have 2 3-way switches need to replace one with a EJ500C timmer
Locate the COMMON wire
connected to first old switch.
It might be attached to a different
colored screw, or find
markings on old switch.
Connect BLACK wire from
switch timer to COMMON
wire, using a twist connector.
Connect the other two wires from the old switch to either the
BLUE and RED wires from the switch timer.
Connect the ground wire from the box to the BARE COPPER
wire on the switch timer. If there is no ground wire, ground the
switch timer to the box. If the box is plastic, connect the bare
copper wire to ground as supplied or contact an electrician.
Locate the COMMON on the second old switch of the 3-way pair.
Connect jumper wire (supplied) from the COMMON terminal
to either of the other terminals on the remote 3-way switch.
Make sure all twist connectors are tight.
Tuck wires into wall boxes leaving room for the devices.
Mount the devices into the wall boxes, then install the wall plates.
Turn power back on at the service panel.
Make sure the switch timer displays “MAN” mode. Do the following
test with the remote switch in each of its 2 positions:
Press the NEXT ON/OFF button on the switch timer several
times. Each time that you push the NEXT ON/OFF button, the
switch controlled light or device (the “load”) should turn on
or off. If so, proceed to Section 3.
If the timer display changes between ON and OFF but the
load does not operate, re-check your wiring and make sure
the load is functional.
If the timer display changes
between ON and OFF but the
load only operates when the
remote switch is in one of
its 2 positions, you need to
turn off the power at the service panel, change the jumper
wire to the other terminal. Then turn power back on at the
service panel and repeat. good luck
Posted on Jan 21, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 28, 2010 | Intermatic Inc. EJ500C Digital Wall Switch...
Nov 10, 2010 | Intermatic EJ500C - Indoor Digital Wall...
Sep 29, 2010 | Intermatic Inc. EJ500C Digital Wall Switch...
May 06, 2010 | Intermatic EJ500C - Indoor Digital Wall...
Feb 27, 2010 | Intermatic Inc. EJ500C Digital Wall Switch...
Jan 04, 2010 | Intermatic Inc. EJ500C Digital Wall Switch...
Oct 20, 2009 | GE Refrigerators
Sep 20, 2009 | Intermatic Inc. EJ500C Digital Wall Switch...
Dec 13, 2008 | Intermatic Inc. EJ500C Digital Wall Switch...
530 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: