Question about Broan-NuTone Fan,Bathroom Exhaust Broan QTXE150
Which wires go together for one switch to operate both the fan and light at the same time
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get to try the service completely Free afterwhich it costs $6 per call and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
If I understand correctly you are installing two wall switches.
Your switches are switch1 and switch2
Each switch has 2 brass-colored screws
If you have a double switch, see page bottom
And you are installing a fan/light combo with separate wires for fan and light.
Bare ground wires and green wires connect to each other and to green screw. A ground wire runs from fan/light to switch box where it connects to other bare copper wire and these wires will not be discussed.
Lets work from the fan/light down to the switch.
Blue-wire-fan connects to either brass screw on switch1
White-wire-fan connects to white Neutral (we'll talk about this wire as we go)
Black-wire-light connects to either brass screw on switch2
White-wire-light connects to same Neutral as White-wire-fan.
So you need 3 wires running from fan/light to your switch box.
One wire arrives at switch box and connects to brass screw on switch1
One wire arrives at switch box and connects to brass screw on switch2
One wire is the Neutral wire and it arrives at switch box and connects to other white wires inside switch box. Twist these wires together and cover with wire nut.
Now your white Neutral is connected to other white wires in switch box.
Each switch still needs another wire.
The Hot black wire from breaker box connects to brass screw on both switches
Pardon the crude drawing.
The switches would actually be located next to each other, but it was easier to draw like this.
Drawing shows 3 wires coming from fan-light to switch box.
The drawing shows the black and white wire arriving from breaker
The drawing does not show how the white wires are joined with a wire nut
If you have a double switch, with 2 switches stacked vertically.
The screw colors can be different.
Double switch could have brass screws on both sides, in which case your Load (fan-light) wires connect on one side of device, and your Hot from breaker connects to other side. It doesn't matter which side, but loads on one side, hot on other side.
Double switch could also have dark screw(s) on one side and brass screws on other side.
In this case, the black Hot from breaker connects to dark-colored screw(s)
And your Load (fan-light) connect to brass colored screws.
If you need more information, or if something is still confusing, answer back.
Posted on Oct 26, 2010
Tips for a great answer:
Aug 26, 2013 | Hunter 52" Ceiling Fan With Light And...
Sep 19, 2012 | Dryers
Nov 16, 2010 | Cooper Wiring Devices Triple Deco Single...
Oct 26, 2010 | Broan-NuTone Fan,Bathroom Exhaust Broan...
Apr 17, 2010 | Broan-NuTone Broan 110 CFM Premium Bath...
Feb 22, 2010 | Leviton 003-1755-W Three Rocker Switches
Jan 06, 2010 | Westwind Classic Hugger Polished Brass 52"...
Jul 07, 2009 | Hunter 52" Ceiling Fan With Light And...
Mar 20, 2009 | Dryers
Apr 28, 2008 | Hampton Bay 24002 Ceiling Fan
76 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: