Question about Rheem Heating & Cooling
Posted by Anonymous on
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
look at circuit board and follow wires that come from fan motor, if this is a standard motor black is high and it will be going to a prong that says cool, red is low and it will go to heat, you will have a yellow and a blue that are "parked" remove red park it were the blue is and put blue on heat, if this is a variable speed motor you will have to set dip switches via your equipment manual
Posted on Sep 30, 2009
You will likely need to install an isolation relay in the W circuit from the thermostat. Some thermostats rob a small current through the W circuit to power the thermostat. This small current can be enough to start the fan circuit timer. You can test this by disconnecting W at the furnace and allowing the timer to shut down. If the fan shuts off with the W disconnected you can install a simple relay.
The relay coil will be connected to Common on one side and the W from the thermostat to the other. Then you will run a wire from R on the furnace to the relay and from the N.O. Contacts to the W terminal on the furnace. This will kill that signal that is starting the timer and the W can steal it's power through the coil back to common.
Posted on May 22, 2010
Tips for a great answer:
Feb 15, 2018 | Heating & Cooling
Feb 18, 2013 | Rheem Water Heaters
Sep 06, 2012 | Rheem Water Heaters
Feb 02, 2012 | Heating & Cooling
Apr 30, 2017 | Heating & Cooling
May 01, 2011 | Whirlpool Water Heaters
Jan 18, 2011 | Rinnai Toyostove Direct Vent Heater:...
140 people viewed this question
Usually answered in minutes!