Question about Rheem Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
look at circuit board and follow wires that come from fan motor, if this is a standard motor black is high and it will be going to a prong that says cool, red is low and it will go to heat, you will have a yellow and a blue that are "parked" remove red park it were the blue is and put blue on heat, if this is a variable speed motor you will have to set dip switches via your equipment manual
Posted on Sep 30, 2009
You will likely need to install an isolation relay in the W circuit from the thermostat. Some thermostats rob a small current through the W circuit to power the thermostat. This small current can be enough to start the fan circuit timer. You can test this by disconnecting W at the furnace and allowing the timer to shut down. If the fan shuts off with the W disconnected you can install a simple relay.
The relay coil will be connected to Common on one side and the W from the thermostat to the other. Then you will run a wire from R on the furnace to the relay and from the N.O. Contacts to the W terminal on the furnace. This will kill that signal that is starting the timer and the W can steal it's power through the coil back to common.
Posted on May 22, 2010
Tips for a great answer:
Feb 18, 2013 | Rheem Water Heaters
Feb 14, 2013 | Rheem RUUD GX90-715A Water Heater,gas,90...
Jan 08, 2013 | Heating & Cooling
Sep 06, 2012 | Rheem Water Heaters
Feb 02, 2012 | Heating & Cooling
Apr 30, 2017 | Heating & Cooling
May 01, 2011 | Whirlpool Water Heaters
Jan 18, 2011 | Rinnai Toyostove Direct Vent Heater:...
Sep 26, 2010 | Heating & Cooling
Dec 13, 2016 | Rheem 13PJL24A01 2 Ton 13 SEER Heat Pump...
105 people viewed this question
Usually answered in minutes!