Question about Rheem Heating & Cooling
I need a transformer 24 volt. Could someone please help me to locate this product i been searching in every plumbing/heating store and even online but there is no help. so please can someone inform me where i can buy this product, in a store or on a website. I live in New York, Long Island. Thanks
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
well it has blown the fuse on the transformer, then you have coil switch bad.It could be the coil on the contath in for cooling.But can check by taking the yellow wire a loose and see if the don't blow. The red wire is one side of the transformer and the com could be any color.But look at the red wire because it is the main wire that travel the voltage throuhg the unit.
Posted on Mar 26, 2009
Check out this website they have a great online rv parts catalog and what is great about this business is if they do not have the part they will find it for you. Never heard of anyone else providing this service but they do and this is why I use them for ordering rv parts for my rv business and my customers.
The website is www.arvparts.com
The Office # is 1-702-762-3428
Hope This Helps!!!!
Posted on Jul 06, 2009
Testimonial: "THanks for the referral"
SOURCE: Blown Transformer heat pump
blown transformers are usually from a low voltage short the first thing i would do is wire a automotive or resetable 3amp fuse in line with the transformer so you dont blow transformer after transformer the wire coming off the transformer that say 24v take that wire a couple of inches down and cut it and install the fuse in series there
now you can go through your low voltage wires one by one and test them unhook all the wires to your outdoor condenser at your indoor unit(furnace or airhandler) and try turning it to cool now if you blow the fuse the short is between the tstat and the indoor unit if the fuse is still good leave it on cool and hook up one wire at a time to your outdoor unit starting with R a lot of times your contactor or your defrost board will short out on you also look for pinches in wires wires with cracks in the insulation and wires touching metal this situation can be a real pain sometimes i would recommend calling a hvac company if you start to get stumped
hope this will help you
Posted on Jul 26, 2009
Tips for a great answer:
Feb 12, 2015 | Rheem Water Heaters
Sep 25, 2013 | Rheem Tankless Hot Water Heater...
Aug 18, 2013 | Water Heaters
Mar 19, 2013 | Rheem Tankless Hot Water Heater...
Sep 07, 2011 | Rheem Water Heaters
Aug 16, 2011 | Audiovox Richmond 6G40-36F 6-Year Tall Gas...
Aug 14, 2011 | Rheem Tankless Hot Water Heater...
Apr 10, 2011 | Rheem Tank Water Heater G75-125, 75 Gallon
Jun 07, 2010 | Rheem Tankless Hot Water Heater...
Dec 13, 2016 | Rheem 13PJL24A01 2 Ton 13 SEER Heat Pump...
107 people viewed this question
Usually answered in minutes!