Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Is the unit an AC only or a heat pump?
Wiring to the units should in the manual or online.
Both units proper house voltage to inside unit and outside unit.There will also be a two wire low voltage cable between thr two.This is so the inside unit can turn on the higher current draw of the compressor in the outside condenser unit thru it's relay.If you have a heat pump there will also be a set of two wires to the 4 way gas valve in the condenser unit to change from heating to cooling mode,a set of two wires to control the on/off function of the fan in the condenser unit when it needs to defrost and mayby a two wire set to a themal sensor in the condenser to sense if it is frosting up when system is in heat mode.
Try to get a wiring diagram and if you can't get to the point where you understand how to wire the unit don't guess! Call someone who knows wiring or call a pro, he can you money over the cost of replacing parts if unit is miswired.
Posted on Oct 06, 2009
Tips for a great answer:
Jan 04, 2015 | Heating & Cooling
Feb 13, 2011 | Heating & Cooling
According to the operation manual your system is low on refrigerant. You will need a technician show up and charge your unit and find the leak. This is a split system so leaks are very prominent.
"U0" Low pressure drop due to refrigerant shortage or
electronic expansion valve failure
A link to the system manual is below.
Hope this helps you with your issues...Jim...please leave a comment
Feb 13, 2011 | Cfm Daikin R410a Split System Air...
Aug 12, 2010 | Heating & Cooling
Feb 25, 2010 | Heating & Cooling
Dec 22, 2009 | Fujitsu 24C1 Air Conditioner
Oct 06, 2009 | Heating & Cooling
Jul 16, 2009 | Heating & Cooling
Mar 01, 2009 | Heating & Cooling
92 people viewed this question
Usually answered in minutes!