Question about Heating & Cooling
After reaching the set thermostat level, my furnace switches to a "fan" setting and blows cold air. Goodman brochure says "Low constant fan allows homeowner to activate the low heat speed to efficiently circulate air throughout the home." It is quite uncomfortable for cold air to be circulated once the thermostat has reached the set temp. I sure would like to DE-activate this option. Possible?
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
There is a little switch on the circuit board. Look closely at the wiring diagram and it will indicate which switch to adjust. If not, review the operating manual for details.
Posted on Nov 25, 2008
first off buy yourself a honeywell stat, in my personal opinion lux stats are garbage, I have run into so many that are bad stats !!! but as far as your fan not shuting down, sounds to me like your fan center on your circuit board is bad and will not shut down the fan when needed, you will have to replace the circuit board, as the fan center is a part of the whole of the circuit board, hope that helps
Posted on Jan 20, 2009
Tips for a great answer:
Jan 29, 2014 | Tools & Hardware - Others
Jun 30, 2013 | Heating & Cooling
Apr 12, 2011 | Goodman CPLE24-1 Air Conditioner
Jan 02, 2011 | Heating & Cooling
Nov 01, 2010 | Goodman Heating & Cooling
Jan 30, 2010 | Goodman GMS90703BXA Heater
Jan 02, 2010 | Goodman GMS90703BXA Heater
Nov 02, 2009 | Heating & Cooling
Aug 03, 2009 | Heating & Cooling
Feb 21, 2009 | Goodman CPLE24-1 Air Conditioner
80 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: