Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
your ac's compraser is getting off due to heat in that area voltage is one of the big issue 2 your thermostat is not working properly of your motor is jammed not rotating properly RPM(running per minute)
Posted on Feb 02, 2010
E-6-Indoor unit heat exchanger sensor [ThIR] defective (resistance is open circuit or closed circuit).
• Poor connection of sensor connector on the indoor PCB.Rectify or replace sensor.
Posted on Jan 05, 2011
That model number is the actual wall controller model number not the air con itself. Go outside get the outdoor unit model number and call actron. Or call an a/c tech to come out.
Posted on Dec 12, 2011
Tips for a great answer:
Jul 31, 2016 | Heating & Cooling
Apr 03, 2016 | Heating & Cooling
Jan 23, 2016 | Heating & Cooling
Jan 01, 2016 | DeLonghi Heating & Cooling
Dec 05, 2015 | Heating & Cooling
Nov 17, 2015 | Midea Westpointe, 12,000 BTU, Thru The...
Oct 09, 2013 | Comfort-Aire 9,000 BTU Mini Split Air...
Aug 01, 2011 | Mitsubishi Mr. Slim MXZ30TN Air...
Apr 05, 2010 | DeLonghi CF210 Portable Air Conditioner
702 people viewed this question
Usually answered in minutes!