Question about GE Zoneline AZ25E12D3B Air Conditioner
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Heat pumps have saftey circuits that prevent liquid flooding of the compressor. Inadequate airflow across the evaporator in cooling can trip this circuit. Have your package unit serviced with particular attention to cleaning the evaporator coil and be sure your filters are clean and changed frequently in the summer months. Hope this helps GL!
Posted on Jun 08, 2008
SOURCE: Short cycling
The most common cause is the fan relay on the main circuit board. However, if the outside temperature is 30degF and the inside is 60-65degF then the cause could be the insulation is ruined or missing on the backside of the unit's firewall. This can cause the unit's internal thermocouple wire to read below 45degF which is the freeze sentinal temp level. Anything below this temp level will cause the unit to come on for a few minutes to warm up the air and bring it to 46degF or higher to protect internal plumbing from freezing.
The best way to check for this is to manually set the unit to one of the heat modes and the thermostat up just until the heater comes on. Let it run until the unit turns itself off. Then set the mode switch back to Off and see if the unit still cycles on and off as before.
If it does then the main circuit board should be replaced unless you are comfortable de-soldering and re-soldering another fan relay in place.
Posted on Jun 23, 2008
Tips for a great answer:
Jun 16, 2014 | GE Zoneline Deluxe Series Cooling &...
Dec 12, 2013 | GE Zoneline Deluxe Series Cooling &...
Sep 17, 2017 | GE Heating & Cooling
Aug 18, 2012 | GE Zoneline In Wall Ptac Unit Air...
Feb 10, 2010 | GE Zoneline Deluxe Series Cooling &...
Nov 09, 2008 | GE Zoneline AZ55H07D Air Conditioner
Sep 05, 2008 | GE Zoneline Deluxe Series Cooling &...
Aug 01, 2008 | GE Zoneline AZ38H12DAD Split System Air...
49 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: