Question about House Brand Heating&Air Conditioning Booster Fan
I have a baseboard water system and I got the air out of the baseboards and I clean them up but it did not work. It could be that the baseboars are to old. The ones in the basement are new.
I can help, but I need a little more info. What kind of boiler do you have, and is it gas, oil, or electric heated, and do you have an air seperator with an expansion tank on it. It basically sounds like you are not moving water through the system. The only to causes for this would be a bad circulator pump, or it is simply air locked. I would check out the circulator pump first. It will most likely be attached to the boiler, and will be in line on the main pipe coming out of the boiler. It is driven by electric, so check out the wiring, and electric supply going to it. There are many brands of these pumps out there. The most common are Taco, Garfundos, and Bell & Gossit. If the pump is pumping, then I would find the highest point of the system and bleed it from there. This can sometimes be a timely undertaking. Just because you are not getting any air out immediately, doesn't mean it isn't there. A good rule of thumb is to take out a gallon of water. If you don't get any air then, your probably good to go. Also remember to make sure your supply water valve is open to put that water back in. Let me know how you do...Rob
Posted on Dec 28, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 15, 2016 | Cars & Trucks
Jan 17, 2016 | Water Heaters
Feb 25, 2011 | Marley Electric Hydronic Baseboard Heater,...
May 29, 2017 | Honeywell Heating & Cooling
Aug 04, 2009 | Heating & Cooling
Feb 20, 2009 | Honeywell Programmable Thermostat Heater
Feb 14, 2009 | Fahrenheat PHH15002 Oil Filled Baseboard...
Jan 04, 2009 | Marley Electric Hydronic Baseboard Heater,...
Sep 11, 2008 | Fahrenheat PHH15002 Oil Filled Baseboard...
Apr 28, 2014 | House Brand Heating&Air Conditioning...
77 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: