Question about Pass & Seymour Electrical Supplies
Posted by Anonymous on
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
#1 cause is a bad lamp,try changing that 1st, 2nd if they are two lamp fixtues you ballast could be going bad/or is. Another solution could be you have a loose common/neutral which is normally the white wire @ the light itself of if it is junctioned @ your switch. I would check those items befor spending the money for a new switch. hope this helps.
Posted on Oct 03, 2009
Yes this is not unusual. Any triac conrol device must have a load large enough to turn it off. I have some switches operating compact flourescnts that do the same thing. My cure was to add one incandescent lamp on same switch, and my load devices work fine too.
Posted on Aug 10, 2010
We also had problems with dimming LED light bulbs until we found these bulbs at LED Lighting Wholesale. Check them out!
Posted on Jun 02, 2012
Tips for a great answer:
Nov 07, 2017 | Office Equipment & Supplies
Dec 12, 2016 | Hampton Bay Dryers
Dec 03, 2015 | Maestro Electrical Supplies
Oct 30, 2015 | Electrical Supplies
Dec 27, 2014 | Electrical Supplies
Oct 11, 2010 | Legrand On-Q/ ALC 600W Dimmer Switch,...
Jan 24, 2013 | Pass & Seymour #696LAGCC6 15A Almond 3WY...
280 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: