Question about Kohler RXT-JFNC-0200A-QS 200 Amp Indoor/Outdoor Automatic Transfer Swi
Did you check the remote terminals and relay in the ATS, disconnect gen remote wires, kill the ATS brealer and ohm across the start terminals, they should close, if not a relay/control board issue, if they do fault is in wiring or gen control, or incorrect wiring
Posted on Nov 27, 2013
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 19, 2015 | Kohler 20resa 20kw Home Emergency Backup...
May 24, 2014 | Kohler Electrical Supplies
Nov 23, 2013 | Kohler OnCue Generator Management System...
Jul 30, 2013 | Kohler 20resa 20kw Home Emergency Backup...
Feb 12, 2013 | Kohler Generator 20kw 20res W/ 200 Amp...
Jan 30, 2013 | Kohler 20resa 20kw Home Emergency Backup...
Dec 16, 2012 | Kohler Generator 20kw 20res W/ 200 Amp...
222 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: