Question about Heating & Cooling
My heater is not working on my ICP Heil Tempstar EBX2400A2
Posted by Anonymous on
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
If no blowing air is coming out to your ac or evaporator fin,your blowing fan is not working.There are several factor to check qualified electrician or ac techician should do this.If you have knowledge on electricity and motor control,beside you should have clamp ammeter to use in trouble shooting of ac electrical circuit.Unplug your ac If there is an opening of blower fan of your ac mostly the top cover open this one locate the wire connection of blowing fan take the color and size.Open the terminal box below the control panel of ac and locate the wire of blowing fan.Check how many leads make sure to make sketch where it was connected from low,medium, and high there is coded color on it,discannect from the terminal, using clamp ammeter set to ohms probe setting R10 check continuinity of winding motor start at common lines(mostly balck color) of one test rod and the other to starting line(mostly red color)take and read the resistance if has a higher resistance your motor is burn out, also with the running line w/c has multple line for speed.If resistance complied to your motor rating or good,If not or burn out replace fun motor.Check your capacitor,doing this set your ohmeter to a higher resistance,connect one red test rod (+) one terminal of capacitor and one black test rod on (-)the other terminal the pointer will deflect steady to higher resistance then reverse the connection of the test rod,the pointer deflect again to higest resistance it will go slow backward setting to zero if you got this result your capacitor is good.But if it does not go set back to zero your capacitor is short.Replaced capaciter.
Posted on Mar 13, 2009
Tips for a great answer:
Feb 07, 2018 | Exercise & Fitness
Sep 09, 2015 | Carrier Heating & Cooling
Jan 22, 2014 | Honeywell ICP Tempstar Heil Furnace Gas...
Nov 21, 2013 | Universal ICP Heil Tempstar 10 12 KW Heat...
Oct 19, 2013 | Fasco ICP Heil Tempstar Furnace Inducer...
Dec 11, 2012 | Honeywell Icp Heil Tempstar Furnace Spark...
Oct 26, 2009 | Heating & Cooling
May 25, 2018 | Friedrich Heating & Cooling
186 people viewed this question
Usually answered in minutes!