Question about Square D Trilliant 100 Amp Circuit Breaker Main
Posted by Anonymous on
Branch loads that are fed by the Main are pulling the amperage to make the breaker warm. Breaker should trip if over 125% of rating
Posted on Mar 31, 2017
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
This work requires a license (or qualified person) everywhere that the National Electrical Code is enforced.
If you're asking how to wire a single phase 200 amp panel from a larger, 3 phase panel of the same voltage - ONE way is to install a 2 pole - 200 amp breaker into the 3 phase panel. Provide 4 correctly sized conductors with the correct insulation in a cable or conduit between the 3 phase panel and the 200 amp single phase panel. Two of these conductors should be black and red (for 120/208 volt system) and connect to the 2 pole - 200 amp circuit breaker terminals, the third should be white and connected to the neutral bus bar. The forth should be green and is connected to the neutral bus bar as well but *only if* it is "service equipment" If it is a "main or sub panel", the green wire should be connected to the ground bus bar. The other end of the conductors should be terminated in a "main lug only" 200 amp panel. The back and red connect to "line 1" and "line 2" bus lugs, the white to the neutral bus bar that is NOT electrically connected to the panel enclosure (do not install the screw or strap between the bar and enclosure). The green must be connected by installing a separate bar that is securely fastened both mechanically and electrically to the enclosure for ground connections.
There is a great deal going on here - and plenty of variables that can change how to do this work, safely and correctly. This is an example of just ONE of many different ways to do the work for a particular installation. There is no one way that works for all situations. If your situation does not support this method - you will have an unsafe installation and subject the building and people in it to a dangerous fire / safety hazard.
Please, consult a licensed electrician before attempting this work.
Posted on Nov 17, 2011
Tips for a great answer:
Nov 17, 2013 | Cutler Hammer "WESTINGHOUSE" MAIN DOUBLE...
Oct 04, 2013 | Bryant /murray Bj2200 Main Circuit Breaker...
Jun 18, 2013 | Bryant /murray Bj2200 Main Circuit Breaker...
Feb 24, 2013 | Electrical Supplies
Oct 06, 2012 | Bryant /murray Bj2200 Main Circuit Breaker...
Jan 21, 2011 | Cutler Hammer 200 Amp Circuit Breaker...
Jun 23, 2009 | Electrical Supplies
Jan 15, 2009 | Electrical Supplies
Dec 15, 2008 | Fahrenheat LFP6152 Halogen Baseboard...
Dec 05, 2008 | Electrical Supplies
Sep 22, 2017 | Electrical Supplies
220 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: