Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Hi , you can try and pull the panel on the bottom of fireplace out and check the adapter in fireplace. Sometimes they go bad. When you open in also check to see if there is an adapter plugged in and a option to use the battery operated function. If this goes bad the pilot will not stay lit.
Posted on Jan 14, 2009
SOURCE: gas fireplace will not stay lit
there is a probe that is in the one of the flame... This once heated builds up enough pressure do to the heat to keep the shut/off valve open... (reason, if the flame went out the gas would continue to flow) this "thermocouple is replaceable !! contact me at firstname.lastname@example.org
Posted on Feb 23, 2009
SOURCE: electric fireplace does not heat
I have a cheap electric fireplace bought in SuperCentre store-heater no longer works. It says its a one piece system. Can these heaters be replaced or repaired(probably made in China) or am i better off scrapping it and buying a new one?
Posted on Oct 18, 2009
You may have a few sensors, one may be a thermopile that energizes the pilot. It is a very thin but long bulb located in the pilot flame. Then you may have something called a thermopile which is also located in the pilot flame that energizes the main gas valve. It is a larger diameter bulb and will have metal wrapped wireg going to the gas valve. If the pilot stays on but the flame goes out under the logs, change your thermopile and look for a bad connection at the gas valve or switch. If both the main burner and the pilot goes out you may have a gas valve problem or a plugged vent pipe. If the flame just disappears it is most likely a gas valve. If the flame changes colors and lifts from the burner, that is a sign of a plugged vent. Good luck.
Posted on Nov 05, 2009
Tips for a great answer:
Dec 14, 2016 | Heating & Cooling
Dec 01, 2016 | Televison & Video
Nov 26, 2015 | Heating & Cooling
Nov 07, 2015 | Heating & Cooling
Apr 04, 2015 | Heating & Cooling
Feb 10, 2015 | Dryers
Dec 02, 2014 | Heating & Cooling
Mar 10, 2014 | Vendor Development Group Inc Borgen...
Jul 05, 2017 | Heating & Cooling
Oct 28, 2010 | Heating & Cooling
27 people viewed this question
Usually answered in minutes!